Undeniably, the maintenance of excellent quality of professional gas boiler for many years also makes more users begin to have more interest in its use. At the same time, it also makes people pay more attention to the quality identification of gas fired boiler. In order to find the right gas-fired boiler equipment, you need to be able to pay attention to the following aspects at the time of purchase.
1. In most cases, concerned about boiler quality, users with certain technical thinking will first pay attention to the boiler quality when buying safe and reliable gas-fired boiler equipment. On the other hand, the performance characteristics and core technology of gas-fired boiler can also directly reflect the excellent quality of gas-fired boiler, which can be evaluated from the product information and qualification honors provided by the merchants, on the other hand, the performance characteristics and core technology of the gas-fired boiler can also directly reflect its excellent quality.
2, pay attention to the boiler cost-performance ratio can be sure that the gas-fired boiler cost-performance ratio is also a focus in the purchase of an aspect, because high cost-effective boiler equipment must be both excellent quality and affordable two advantages of the characteristics of the two advantages, The benefits of such a choice not only give users a sense of real value for money, but also avoid questions about how much more gas-fired boilers cost more than coal.
3, pay attention to customer word of mouth in addition, when choosing a good gas boiler, you should also refer to the past customer's specific evaluation of this equipment, and these contents are actually available on the boiler brand's official website, At this time, we can get a comprehensive understanding of the professionalism, usability and safety of gas-fired boiler equipment through the real evaluation of these past customers, and then we can find out the better boiler equipment in the word-of-mouth as soon as possible.
So now some corporate buyers, might face the problem of distributor 6t boiler moldavia equipment selection and purchase of the equipment for such boilers choose when to go or should take into account the energy aspect of it, such as boiler plant, is the emergence of many different forms of energy, such as electric boiler equipment now, there is natural gas. And making choices, it should also take into account the current boiler equipment, in terms of security it is how, is not able to have a good operability and so on.
Battle blue horn sounded, emissions of sulfur, nitrogen and oxygen compounds gradually strict national requirements. To improve the quality of the environment, but also the people a blue sky, in all industries around the environmentally friendly product revolution, Hainan Sinochem Pharmaceutical companies are no exception. By the company investigation and comparison of distributor 6t boiler moldavia products, in March 2017 signed a six-ton steam-cleaning integrated condensing gas boiler and steam fast boiler. Tested and post feedback, the boiler equipment installation qualification, operating normally, and successfully passed the inspection by local quality inspection departments of the boiler.
You must know the distributor 6t boiler moldavia energy problems (induced draft fan power consumption rate, steam consumption) draft fan causes problems 1.1 boiler flue dust and fouling, in particular air preheater fouling, resulting in increased resistance to smoke duct . 1.2 boiler flue, tail heating surface and dust leakage. 1.3 Leakage Rate large air preheater. 1.4 furnace excess air coefficient is too large. 1.5 unit load changes, run the adjustment is not timely, resulting in furnace pressure is too large. 1.6 unit load or low frequent starts and stops. 1.7 coal into the furnace worse, from the design value. 1.8 low efficiency filter. 1.9 draft fan blade badly worn, low operating efficiency. 1.10 fan outlet flue gas desulfurization big resistance. 1.11 soda boiler pipes for leaks. 2, 2.1 to 2.1.1 operational measures to solve the problem of the strict implementation of soot blowing system to prevent the heated area ash, blocking ash, flue gas system to reduce resistance. 2.1.2 holding the induced draft fan, the flue gas separator baffles and dampers in the fully open position. 2.1.3 The experiment showed combustion boiler, proper control of excess air in the furnace. 2.1.4 adjustment chamber negative pressure, air leakage reduction furnace and the flue. 2.2 routine maintenance and testing 2.2.1 induced draft fan performance test to determine the optimum operating point and efficient workspace. 2.2.2 boiler, air preheater, a flue, ESP and other system leakage inspection, process. 2.2.3 timely check processing chassis, shaft seal leakage. 2.3C / D repair, eliminating defects 2.3.1 down strict accordance with movement clearance adjusting fan. 2.3.2 induced draft fan blade defect action elimination hand vane opening adjustment. 2.3.3 Importers and induced draft fan baffle opening check. 2.3.4 duct tightness check process. 2.3.5 wave plate replacement air preheater, rinsed sector plate gap adjustment. 2.3.6 eliminate dust defects and improve collection efficiency. 2.3.7 clean flue gas desulfurization system, flue resistance is reduced. 2.3.8 eliminate soda boiler pipe leakage defects. 2.4A / B repair and transformation 2.4.1 Check and repair the fan blades, replace seriously damaged blades if necessary. 2.4.2 for energy saving fan efficiency below 75%. 2.4.3 The fan motor frequency transformation. 2.4.4 of the precipitator, if necessary, transform and improve collection efficiency.