Select the first 6 ton coal fired steam boiler for sales to know what parameters? Steam boilers have the following main parameters: 1, Rated evaporation Rated evaporation is power steam boiler, steam boiler is the most important parameter, usually expressed in tons evaporation, that is, we usually say how many tons of boiler. 2, rated steam pressure rated steam pressure means that the steam pressure generated in the steam boiler, generally expressed in MPa or kg. 1MPa is 10 kg, like laundry, all hospitals, factories and the like conventional steam occasions the general use of low-pressure steam 1.0MPa or less. Only when using steam as a power to require the use of high-pressure steam. 3, where the steam temperature of said steam temperature, refers to the temperature of saturated steam. Saturated steam pressure and steam temperature are corresponding. Temperature of saturated steam at a pressure of 1MPa 184 ℃. 4, gas / oil / coal consumption fuel consumption is an important indicator of concern when choosing a steam boiler, which is directly related to the use of the running cost of the boiler. In the operation of the boiler, the fuel cost is very impressive, if just considering the purchase cost of buying a cheap but high energy boiler, which led to the late high operating costs, certain that it will be wasted. 5, the thermal efficiency of fuel consumption with the boiler thermal efficiency of boilers is inversely proportional. The higher thermal efficiency, lower fuel consumption of the boiler. Boiler thermal efficiency expressed as a percentage, the value is a more intuitive. 6, the boiler operating weight, size or location in the election of the steam boiler, it should find the place whether the load per unit area can withstand the weight of the steam boiler, and if there is enough space to place the steam boiler maintenance and reserve space.
Coal fired boiler design features:
1.By adopting of double wings gas ducts, the fuel gas can go into the front gas tank easily, so the temperature of different front plates can be same. In this way, it can avoid the crackles happening in the plates.
2.Spiral tubes are installed in the drums, which can strengthen the heating transferring efficiency, at the same time, spiral tubes have the ability of dust removal, which can avoid the dust stratification in the tubes.
3.Both of the front and the back arches of the 10t/h series coal fired boiler design adopt mason work of water cool tubes wall structure, which can form permanent arches.
4.Separate adjustable wind chambers. Wind is feed from two sides. It adopts new type crank screw wind adjustment structure, so that the wind adjustment and ventilation cross section proportion is 100%, which can ensure the easy wind adjustment and make it symmetrically.
5.There is push-pull damper dust removal equipment. The damper adopt finish machining cast iron seal structure, thus the secondary combustion distortion and air leaking in the grate is effectively prevented.
In a pressurized fluidized bed boiler, the entire fluidized bed combustor is encased inside a large pressure vessel. Burning solid fuels like coal and biomass in a pressurized fluidized bed boiler produces a high-pressure stream of combustion gases. After the combustion gases pass through a hot gas cleanup system, they are fed into a gas turbine to make electricity, and the heat in the hot exhaust gas stream can be recovered to boil water for a steam turbine. Therefore, a pressurized fluidized bed boiler in ZG company has high efficiency and good performance. Each year, ZG invested a lot of money on pressurized fluidized bed combustion technology. Higher techonology and better efficiency is ZG Boiler pursue.
The safety inspection operations will be based on "regarding the development of boilers and industrial emergency notification equipment and facilities safety inspection of" (Wei Safety Office Zi  No. 23) documentation requirements, earnestly implement the regulatory responsibility, and actively carry out arrangements, combined with Cravens practical, clear pressure boiler safety inspection work content and division of tasks.
In conjunction with the National Health City welcome the review investigation work, based on their job functions, all members of the team to take the sinking line, full package by, Division linkage approach, focusing on whether the boiler to handle the use of registration, whether periodic inspection, workers who whether induction certificate, the safety valves and pressure gauges and other safety accessories boilers are using the site regularly check verification, the highest level gauge whether there has been a minimum level of safety markings for verification. 54 boiler region's 24 units were one by one investigation. Up to now, all 33 units in the boiler are in an examination period, in line with the requirements. It has two boilers to handle the deregistration, and 19 boilers have long-term disabled, is now urging the use of units to seize deregistered.
While actively step up publicity and training efforts, and send more professionals to communities, cooperatives were the main person in charge of safety knowledge of professional training, to explain the basics of boiler and check focus, effective universal safety knowledge, improve regulatory efficiency.