The meeting also outstanding performance in 2016 was in recognition of outstanding dealers, Lu president called on everyone confidence, walk hand in hand, writing a new chapter in the rapid development of the fast side. After the meeting, the participants went to the factory, gas efficient anthracite coal hot water dhl boiler laboratory site visit. Then, fast boiler dealers a VIP Tong Fu Australian business communication, to visit and learn advanced foreign technology. The meeting has come to an end, fast-party reseller partners to do with the group to explore strategic, content exchange, policy interpretation, experience sharing, so that the two sides closer together, you and the dealer is confident it can work together under the leadership of the party soon Group creating a potential win-win future.
The working principle of hot water boiler is very simple, which depends on the heat energy of fuel combustion to achieve the function of heating water, it is a kind of simple heat energy boiler. Hot water boiler is one kind of boiler, mainly because its medium is hot water. There are many kinds of hot water boilers, which can be divided into point hot water boilers, oil hot water boilers, and some more environmentally friendly gas and coal fired hot water boilers according to the fuel used.
After statistics, we found that water tube boilers are a very popular type of furnace in Malaysia, especially biomass boilers. The water tube boiler is a boiler in which water, steam or steam-water mixture flows in the pipe while flame or smoke burns and flows outside the pipe. If the fuel is coal or biomass, the water tube boiler type is SZL double drum type or DHL corner tube type, if the fuel is gas or diesel, the SZS double drum is main type.
Steam efficient anthracite coal hot water dhl boiler rules Henan fast boiler with small series to introduce the company's steam boiler operating procedures. First, the components of the steam boiler before oven cooking oven and check (a) and oven cooked boiler furnace must be checked in detail. Check the following items: 1, cold chain grate test more than 24 hours, cold test should meet the following requirements: (1) grate should be smooth turning chain wheel axle, found arched, two tension bolts can be tightened. (2) the active grate sprocket good occlusion. Minimum gap (3) on both sides of the active grate block with the side seal and the side seal angle not less than 6 mm. Distance (4) on both sides of both ends of the furnace grate platoon leader pin in the sprocket should be kept equal. If it is found at one end to the occurrence of side friction, long waist-hole may be a tap with a hammer, the end surfaces on both sides remains equal distance. (5) steam boiler grate rotated without jamming, deviation phenomenon, when the deviation found by the inspection hole into the rear grate tail, the tie bolt align the two bearings of the drum, deviation phenomenon can be eliminated. The boiler has ignition combustion, still need to transfer found Hearth n, just before two adjustable chain tensioning bolt shaft directly outside the furnace, but preceded align the front sprocket shaft and a gearbox connect the safety pin or bolt removed until after squaring shaft to a gearbox with a chain alignment pin or bolt after tightening, may otherwise result in misalignment with the sprocket shaft of a gearbox and mechanical damage. (B) Check broken grate furnace platoon leader pin is bent, if long waist hole in the furnace may be carried out at any time platoon leader pin alignment reload. (C) a chain grate does not allow foreign matters (such as bolts, nuts, nails and other iron) is present. (D) firing door open and flexible, easy to open and drop the shutter coal, coal gate left and right side of the grate surface distance equal to, the thickness of both sides of the seam to ensure equal furnace, as a method for reducing ranging from links available to make equal, coal shutter cover plate should cover tightly to prevent leakage into the coal, coal stuck shutter. (Five) of each grate windshield of smoke damper and damper adjustment inside the flue flexible switch. (Vi) blower, Fan, Java machine, commissioning normal water supply equipment. (Vii) manhole, hand hole is tight, attached parts fitted Ge are complete. (Viii) the furnace wall is normal, the flue is tight. (Ix) steam boiler pipes, water pipes, sewage road is complete. (J) all filled with lubricating oil in the bearing housing and oil cup. (Xi) All electrical equipment should be empty running test, inspection equipment, and other electrical lines is intact.