In recent years, the state environmental protection is all the more attention we as a company with the times, in order to respond positively to the implementation of the national environmental protection requirements from coal to gas project. But the choice of boiler suppliers in this area quite a headache, after repeated comparison and investigation, we chose to partner with fast boiler. Fang did not disappoint quickly proved that the recommended boiler operation after use to fully meet our needs, both energy saving and environmental protection, high thermal efficiency, to a certain extent, cost savings for our fuel. --customer feedback
Purchase Price:Quality never comes cheap but don’t overspend. Buying a condensing boiler for a non-condensing application is like paying extra for a hybrid car and then throwing away the batteries. Rite offers multiple boiler lines - for the boiler you need - at very competitive prices.
Check the contents of the auxiliary boiler operation:? 1 fan: Manhole closed tightly, the bearing temperature indicates the correct temperature <70 ℃, front and rear bearings normal oil level 1 / 2-2 / 3, bearing oil level is normal, backwater normal, return water temperature <40 ℃, shaft vibration <0.1MM, string axis <2 --- 4MM, the normal rotation of the fan, without friction, abnormal sound, no smell. 2, the motor Motor no loose anchor bolts, screws shroud wheel well, firm ground line, front and rear bearings normal oil level, the oil level gauge clarity, good oil, bearing temperature <70 ℃, motor temperature <100 ℃ motor shaft shock <0.1MM, string axis <2 --- 4MM, the normal rotation of the motor, no friction investigation, different tone. 3, the baffle: an inlet baffle adjustment operation flexibility, good link is coupled with the actuator, indicative of the correct scale, the local switch - remote control - the position of the outlet shutter flexible movement of the link mechanism is coupled perform well, indicating proper scale , local switch, the - remote control - the position of 1 / 2-2 / 3.4, petrol stations normal oil tank, good oil, hydraulic oil pressure adjusting 2.5-3.5MPA leakage of hydraulic oil oil oil return to normal, lubricants 0.4 --- 0.5MPA filter differential pressure <0.05MPA, lubricating oil normally adequate oil return, the system no oil, the cooling water flow, normal tap water, the return temperature <40 ℃. 5, the bearing housing normal oil level, oil well, a temperature of <60 ℃.
Good gas boiler operation safety procedures can effectively extend the life of gas-fired boiler, then how to properly regulate the operation of the gas boiler it? Detailed below: 1, when a boiler or endanger the safety of the phenomenon should be taken to an emergency shutdown; 2, boiler feed water pump damage, mediation device failure, emergency disconnect button should move to stop the boiler operation; 3, the boiler in operation Once the process anomalies operators should be shut down immediately after the new boot deal with failure; 4, when the gas boiler body found abnormal phenomenon, how to do security incidents shutdown control device failure should move off the emergency button to stop the boiler operation; 5, start and stop by the boiler burner controller is to issue an instruction start and stop according to a change in pressure, (this function is automatic) the operator should always observe the change in the pressure abnormality occurs to stop immediately if the cease-fire; 6, You should always observe the water level, in particular to ensure that the boiler operation fill the tank full of water during operation. The operator shall periodically to the boiler blowdown, boiler water quality assurance. 7, when there should take in electricity fuels Pressing the emergency OFF button; 8, should be determined prior to the initial startup burner with three-phase power operator motor forward, reverse, or can not normal ignition. (At this time, the fan stops burner ten seconds after the start, the alarm control box). Understand the safety procedures gas boiler, I believe you must have learned a lot of knowledge of it, I hope to help you prolong the life of the boiler