Class B, a predetermined alarm and an oil pump Heat Transfer Material Heater described organic heat boiler, which is a boiler, but also the more common and popular. So, based on this, then, will explain the boiler-related knowledge, so that we can know and understand it, and at the same time, can increase their expertise in this area. So, based on this, then, will be immediately proceed to enhance everyone's learning efficiency. 1. Organic Heat Carrier boiler organic heat carrier, which specifically refers to what? It belongs to the hazardous chemicals it? In addition, B-class boiler, is how these two provisions of the vapor and liquid organic heat carrier boiler? Organic heat carrier boiler organic heat carrier, the specific terms of the case, which means that thermal oil is an oil. Due to its ignition point and flash point is relatively high, therefore, does not belong to dangerous chemicals. And Class B boiler, gas and liquid phases of the two predetermined specific species, is: Q is greater than 0.7MW gas furnace, the furnace is liquid Q is greater than 4.2MW. 2. Organic Heat Carrier boilers, pumps and expansion tank low level alarm, whether there is a connection? Organic Heat Carrier boilers, pumps and expansion tank low level alarm, there is no necessary connection, because, pump alarm, there is only pressure alarm, and the expansion tank low level, it is a lack of oil expansion tank, which when should oiling system to perform work up the oil. 3.G1 certificate, which it can operate the boiler will be? Among them, this one contains organic heat carrier boiler? G1 syndrome, type boiler which can operate, for: rated pressure not greater than 0.4MPa, and the evaporation amount is not greater than the rated 8t steam boiler distributor 0.5t / h of. In addition, there is not greater than the rated power of 0.7MW hot water boilers and organic heat carrier boiler two boiler. These questions are all about this kind of boiler organic heat carrier boiler, and also we must know and master, because the only way to make yourself and learn something instead of nothing. And, for us it is also a very good opportunity to learn, therefore, should cherish is.
Battle blue horn sounded, emissions of sulfur, nitrogen and oxygen compounds gradually strict national requirements. To improve the quality of the environment, but also the people a blue sky, in all industries around the environmentally friendly product revolution, Hainan Sinochem Pharmaceutical companies are no exception. By the company investigation and comparison of boiler products, in March 2017 signed a six-ton steam-cleaning integrated condensing gas boiler and steam fast boiler. Tested and post feedback, the boiler equipment installation qualification, operating normally, and successfully passed the inspection by local quality inspection departments of the boiler.
The electric boiler, also known as the electric water boiler, the electric drinking water boiler, the electric tea boiler, and the electric tea stove, is divided into two types: continuous electric water boiler and split tank electric water boiler, which are designed to meet the needs of more people drinking boiled water. A kind of drinking water equipment using electric energy to produce hot water is developed, which is mainly suitable for the use of schools, hospitals, factories, supermarkets, shopping malls and other population-intensive units. The main component of the electric water heater is the electric heating tube which plays the role of heating. It is better to choose the electric heating tube with insulating material, which has high safety factor and long service life. Under normal conditions, it can work for 6-7 years. The electric hot water boiler is also called the electric heating boiler, the electric bath boiler, etc. The electric hot water boiler is the production hot water that adopts the latest electric heating technology and the control system design, satisfies the heating or the supply life, Fully automatic environmental protection boiler of hot water for bath. This kind of boiler is suitable for hot water and heating in hotels, villas, factory buildings, office buildings, government agencies, colleges and universities, hospitals, troops and other places with high appearance requirements. The electric boiler is divided into two types: direct heating type electric boiler and regenerative type electric boiler. As the name implies, the direct heat type electric boiler is no longer explained here, and the regenerative type electric boiler is based on The power sector encourages electricity heating during trough periods and enjoys preferential electricity prices, introducing a new, efficient and energy-efficient electric heating product. Regenerative type electric boiler is composed of heat storage water tank and auxiliary equipment, which makes use of hot water heating in heat storage tank to achieve the goal of using all or part of the low valley power from the purpose of making use of the hot water in the heat storage tank. Electric 8t steam boiler distributor is also called electric steam boiler. Electric steam boiler is a steam boiler which uses power source to heat and produce rated pressure. Steam boilers can be used in textile, printing and dyeing, paper making, food, rubber, plastics, chemical, pharmaceutical, iron and steel, metallurgy and other industrial products processing process Steam is required and can be used for heating, bathing, air conditioning and hot water in enterprises, institutions, hotels, schools, catering, and service industries.
01. The reason why the ignition rod of gas-fired boiler burner does not ignite: 1. There is carbon slag in the gap of the ignition rod, there is oil pollution. 2, the ignition rod is cracked. Damp. Leakage. 3. The distance between the ignition rod is not right, too long or short. 4, the distance between the ignition rod is not right, it is too long or short. 4. Ignition rod insulation outer skin is damaged, short circuit to the ground. 5, ignition cable and transformer failure: cable broken, connector damage caused by short circuit fire; The transformer is out of line or out of order. Gas-fired boiler burners failure, ignition rod non-ignition treatment measures are as follows: clear, replace, adjust distance, change wire, change transformer. Second, the reason why the ignition rod of the gas-fired boiler has sparks but does not ignite: 1. The ventilation clearance of the cyclone disc is blocked by carbon deposition and the ventilation is poor. 2, the oil nozzles are unclean, clogged or worn. 3, the setting angle of the air door is too small. 4, the distance between the tip of the ignition rod and the leading edge of the oil nozzle is inappropriate (too prominent or indented) 5, The solenoid valve of the first oil gun is blocked by debris (small fire gun) .6, the oil quality is too viscous to flow or the filtration system is clogged or the oil valve is not opened, which causes the oil pump to absorb insufficient oil, the oil pressure is low. 7, the filter of the pump itself is blocked. 8, Oil contains more water (boiling noise in heater). The measures to deal with spark but not ignition of ignition rod of gas-fired boiler are as follows: clearing; cleaning first, if no replacement; adjusting test; adjusting distance (3~4mm is good); remove cleaning (cleaning parts with diesel); check pipes and oil filters, insulation equipment; remove oil pump outer screws, carefully remove the outer cover and remove the inside net, wash with diesel; replace it with new oil. Third, when a small fire of a gas-fired boiler is turned into a fire, the reasons for its extinction or flickering instability are as follows: (1) the air volume of the air outlet of the fire is set too large. 2, The oil valve fretting switch (the outermost group) of the fire is improperly set (set higher than the air flow of the fire valve) .3, the viscosity of the oil is too high and not easy to atomize (heavy oil). 4, the distance between the cyclone disc and the nozzle is inappropriate. 5, To wear or soiled the nozzles of a fire. 6.The heating temperature of the reserve oil tank is too high, causing the steam to cause the oil pump to send oil unsmoothly. 7, the oil in the burning oil and gas hot water boiler contains water. Treatment measures to extinguish or flicker unstable when small fire of gas-fired boiler turns to fire normally: reduce test step by step; raise heating temperature; adjust distance (between 0~10mm); clean or replace; set about 50 ℃ or so; change oil or drain water. 4. Causes of noise increase in gas boiler burners: 1, shut-off valve or insufficient oil intake in the oil path, blocking of oil filter. 2, low inlet temperature, too high viscosity or too high intake temperature of pump. 3, oil pump failure. 4, oil filter blocking. 4, oil inlet temperature is low, viscosity is too high or pump inlet temperature is too high. 3. Fan motor bearing Damage. 5, fan impeller is too dirty. Treatment method for increasing noise of Burner in Gas-fired Boiler: (1) check whether the valve in the pipeline is open or not, and the oil filter is working normally. Cleaning pump itself filter screen. 2 oil heating or lowering oil temperature. 3 replacement pump. 4 replacement motor or bearing. 5 cleaning fan impeller.
01: the greatest benefit of economic use of gas-fired steam boilers is that they can save large amounts of material costs for enterprise users, without the need to spend heavy money on large amounts of coal-carbon fuel. Only clean natural gas can be used to burn and release the steam used. Natural gas can also increase the thermal effect and reduce the cost of material input for users. Safety: natural gas is well known as one of the safest non-toxic and pollution-free clean fuels, unlike liquefied gas or gas leaks that precipitate on the ground and even cause accidents. Gas-fired steam boiler is the safest way to choose natural gas in the process of transporting gas, and it is easy to leak. Being found to be used is therefore the safest way to use it. 3: the convenient gas-fired steam boiler is also the most convenient one in use, so it will be favored by the customers of various enterprises. Natural gas pipelines are as convenient as tap water for domestic use, and sustainable use will not be bothering you. It eliminates the cumbersome work such as transporting or stacking coal and cleaning coal residue. 4: clean gas-fired steam boilers are highly rated in the market because they are clean and clean in use and free of black pot bottom and exhaust gas pollution. So it's cleaner than any other boiler in use. One way, whether directed at operational work or surrounding residents or the business itself, can be cleaner without compromising physical and mental health.
To get industrial gas boiler safe operation must be done to check the work of industrial gas-fired boiler pressure vessel belongs, in our country there are strict and clear standards of production and operation. In particular boiler in operation, should always pay attention to whether the safe operation of the boiler, auxiliary equipment and operation of each respective instrument valves is stable. Therefore, gas 8t steam boiler distributor room is necessary to establish a sound system of inspection tours and boiler room equipment maintenance system. First, natural gas boiler room mobile inspection system 1, in order to ensure the normal operation of the boiler and its accessory equipment, timely detection of problems, fireman on duty personnel at least once every half hour tour inspection. 2. Check gas boiler burners, pressure gauge, thermometer, circulation pump, water supply pump, water softening, safety accessories, an instrument, secondary instrument is functioning properly. 3, check whether the abnormal changes in various types of signal lights. 4, check the water level in the tank gas boiler, feed pumps, circulating pump and motor bearing temperature and pump lubricating parts are normal. 5, check the position of the gas valve and the steam boiler feedwater pressure switch valve is normal. 6, mobile inspection found problems in time, and test results recorded in the log boiler and accessory equipment inside. Second, gas-fired equipment maintenance system 1, two gas-fired boiler on the pressure gauge value is not the same timely maintenance, to ensure reflect the actual operation of the boiler pressure. 2, gas boiler pressure gauge damage, when the dial is not clear, timely replacement. 3, rotating machinery lubricating oil passage remains open, the oil cup to maintain a certain oil level. 4, run, run, drip, leak repair valves can be repaired, replaced. 5, inspection, maintenance and feed pumps, circulating pumps and pump valves open is flexible, single-stream if the door is closed tight. 6. Check the gas-fired secondary instrument is normal. 7, to remove dust on the equipment and the accessory device. 8, check the gas boiler safety valve manually turn on the water after closed trials are tight. Automatically turn on the water, blowing off steam at least once a week. 9, pressure gauges operate properly flushed at least once a week. Trap maintenance once a month. 10, over-temperature, overpressure alarms, overpressure interlock device checks at least once a month, and maintenance. Gas boiler pressure gauge, water level gauge and a safety valve are the three safety accessories on the gas steam boiler, with particular attention.