Main steam boiler temperature abnormal phenomenon of how to do 1, main steam temperature anomalies alarm. 2, the rapid variation of the main steam temperature, a secondary damper frequently significantly reducing water operation. 3, starting superheat outlet steam separator above or below normal. 4, if the steam with water, the unit will water shock occurs. 1 reason, the fuel and water supply imbalance, the separator outlet temperature abnormality. 2, coal combustion conditions change or affect, such as excessive load lift; and pulverizing mill administration system abnormality stop; means automatically increase or decrease the failure rate is too large amount of wind and the like. 3, the central flame furnace changes, such as the bottom seal damage, W and inadequate flame downstroke. 4, the control failure by warm water, warm water flow rate reduction is abnormally reduced or increased. 5, feedwater temperature mutation. 6, does not match the wind coal. 7, the secondary combustion heating surface. 8, furnace coking or fouling seriously. 9, heating surface leakage squib. 10, flue gas damper opening degree is not normal. 11, coal sudden change occurred. 12, the uniformity of the powder feeding substantial change occurs. 1 process, failure caused by unit coordinated coal - water ratio should be immediately released coordinate offset, in accordance with the current load demand, with reference to the start of the steam superheat separator, and adjusting the amount of fuel corresponding to the amount of water, with one, two main desuperheating water rapidly steam temperature control in a normal range; when the coal - water ratio should avoid imbalance after coal and water while adjusting; when coal - water ratio is adjusted to further adjust the load after a relatively stable; contact maintenance processing timely. 2, when the water supply system fault condition occurs a significant disturbance furnace should pay attention and automatically coordinated working conditions, so as not to manual intervention, when not working properly coordinated and automated, should be manually adjusted, stable water flow, referring to separation according to the water flow steam superheat, the adjusted amount of fuel, with a secondary spray water rapidly controlling the main steam temperature within the normal range; contact maintenance processing timely. 3, due to rapid changes in load caused by the load change rate should be adjusted; load change caused due to protective operation or the like caused by heat load to be quickly adjusted to maintain the boiler pressure of the main steam stability. 4, by warm water automatic dysregulation, should be appropriate Save warm tone is switched to the manual may be an intermediate point of the feedwater control system be corrected for temperature if necessary, or the feedwater to switch control to manual control, due to lower lifting and lowering the load speed to prevent steam temperature, promptly contact a service process. 5, the boiler furnace cause severe fouling and coking of the main steam temperature anomalies can be corrected by an appropriate degree of superheat outlet steam separator start, adjust, and in a timely manner and the furnace heating surface sootblowing. When the platen superheater sootblowing or superheater outlet temperature is still above normal and a secondary reducing water damper fully open, to check the furnace and the combustion air distribution system is normal, the checking process to reduce still overtemperature unit load. 6, flue gas damper adjusted to an appropriate opening degree. 7, if the bottom seal after losing back to normal immediately. 8, to strengthen the turbine expansion, differential expansion, axial displacement of the shaft vibration and bearing temperature monitoring, if abnormal, the process according to the corresponding regulations. 9, after the above measures, if invalid, should immediately drop the load process. 10, in front of the main steam temperature main steam 50 ℃ drastically reduced within 10 minutes, should an emergency stop.
58MW SZS series gas-fired why the burner of coal hot water boiler can not ignite project for heating industryPeople cannot live a comfortable life without heating boilers in the winter, the normal and stable heat source is of great importance to human life. What is following is the increasingly serious problem of environmental pollution, implementing the policy of “coal to gas” is no time to delay, using gas-fired hot water boilers has been the general trend. Tianjin Jizhuangzi heat supply center is an enterprise specializing in city heat supply. In order to realize the “green heating”, the heat supply center decided to introduce a branch of gas-fired boilers to replace the old coal-fired boilers. ZOZEN successfully won the trust of Jizhuangzi heat supply center with its own strong comprehensive strength and rich experience in the heating industry. JIzhuangzi chose to cooperated with ZOZEN and ordered 3 sets of 58MW gas-fired hot water boilers (SZS58-1.6/130/70-Q) to provide heating source for citizens. This series of boilers adopts the design of " D " type membrane wall structure, the steam drum, the water drum and convection tube bundle form the convection heating surface to ensure the the boiler expands on both ends as a whole; at the same time, the combustion chamber is designed with the narrow distance tube membrane water cooling wall to reduce heat lost, in addition, the boiler is equipped with a big combustion chamber for the full combustion of fuel, effectively increasing the boiler thermal efficiency over 98% and reducing the NOx to 30mg, which are superior to the national level one energy efficiency standard.
What part of the body including the boiler? What role have? It comprises a crucible and the furnace: a body: refers to a soda boiler system, which is superheated by the reheater water preheating system and a vaporization system composed of dry steam. The role of the high-pressure boiler feedwater heater through the further heating evaporation, for the purpose of blowing rpm turbine to do work. System configuration: economizer, the drum, the downcomer, water wall, superheater, reheater, economizer high pressure heater outlet feedwater is introduced into the economizer, economizer tube within an outer absorber tube gas and fly ash heat, water temperature increases to about 300 ℃ drum water out from the economizer line into the bubble along the top of the boiler disposed outside. Drum lower half of the water, the upper half steam. Unsaturated high pressure drop along the water reaches the bottom of the bubble tube at the bottom of the lower header outside the boiler, a number of pipes mounted in parallel on the bottom of the boiler around the lower header, the furnace by the upward flow of the absorbent in the central flame of the inner tube wall pipe convective heat radiation heat transfer and high temperature flue gas. Since the heat absorption is much less than the water vapor, the water wall within a predetermined vaporization rate can not be greater than 40%, because the working fluid will easily melt late Wall water absorbing tube rupture occurred. Downcomer role is water vapor to the bag waterwall lower header, to establish a water circulation. Wall water in the tank through the second line and then returned to the boiler water wall, the water in the drum is completed, the downcomer, the circulation between the superheater waterwall separated in the steam drum is withdrawn from the top of the drum, laying into the first top ceiling superheater, then through the cladding wall superheater, low temperature superheater, platen superheater, to a high temperature superheater, after reaching the rated temperature of the heating steam turbine into work. After the reheater boiler is also provided with a large reheat means that steam from the high pressure cylinder acting, temperature and pressure of the exhaust gas is reduced, the exhaust gas is heated to a reheater, and then returned to the steam turbine, a low pressure cylinder continues to work. Furnace body: it refers to a boiler furnace combustion system and its role is to heat the fuel combustion in the furnace as much as possible and transfer heat to the working fluid, and the completion of the water wall and economizer water water heated in the tubes, heated in the dry steam superheater and reheater tubes, the air in the air preheater tube heated. The system consists of: a combustor, furnace, air preheater. Production process: raw coal from the coal by the belt conveyor to the higher field position of the coal bin, the bottom of the coal from the coal bin out through the stoker evenly into the ground to a coal mill. Nature of the atmosphere via the air inlet of the blower is arranged in the vertical flue to the boiler air preheater, subjected to heat of the flue gas, flue gas waste heat recovery. About 250 degrees out of hot air into two air preheater from: one directly introduced into the burners of the boiler as secondary combustion air into the furnace; the other can be introduced into the mill inlet for drying, transporting coal, which said primary air portion of hot air. Excellent flow of drying gas and pulverized coal mixture powder consisting of primary air, conveyed via line separator to be coarse coarse separator, the separated coarse powder inlet sending back regrind mill, and eligible powder and primary air mixture into pulverized powder separator, gas separation, the separated coal fines into storage to save it from the powder according to the magnitude of the thermal load of the boiler, the control of coal flow discharged coal warehouse bottom while separated from the fines separator as the primary air pulverized coal power delivery, after the pressing of mill powder mixture with the gas mixture into a fine powder fed again by a burner into the combustion furnace.
Fangkuai Group adopts the concept of “moulding character and creating high-quality products”, and continues to research and continuously improve the technological content of products to get closer to users. With the mission of “creating convenient and fast boiler high-quality products for users”, it uses remote monitoring, APP, and active return visits. And other channels to provide users with convenient and efficient services; with the core values of "professionalism, lean work" as the core value, established an effective enterprise management system, adopted ISO9001 quality management system, OHSA18001 occupational health and safety management system and ISO14001 environmental management System certification; and cultivated a large number of high-quality employees with norms of behavior, professionalism, and continuous commitment to provide customers with more convenient and efficient services.