Gas Steam Boiler non-normal stall, a phenomenon and treatment, flame reasons: 1, the operation of the auxiliary power supply or trip interruption. 2, boiler combustion instability. 3, the load is too low, so that the load sharply mill automatic ignition energy loss or failure of combustion. 4, mutant coal, coal volatile or low calorific value. 5, the automatic combustion flame detector failure or failure caused by tripping mill. 6, or blast furnace wall tubes serious improper boiler soot-blowing operation, a large amount of water vapor into the combustion chamber. 7, coal pulverizing system, fuel system failure, resulting in a significant amount of fuel reduction or interruption. Or with a large amount of water in the fuel oil gun blocked too many impurities, low pressure steam or atomized. Second, the phenomenon: 1, a significant increase in furnace pressure, furnace flame monitoring flameless CRT display. See the fire no fire hole, BTG warning window MFT warning lights. 2, the unit load decrease, the steam flow drops rapidly, each segment working medium temperature, the vapor pressure decreases, the value of oxygen surge. Third, the method of treatment: 1, if the MFT tripping protection, should an emergency shutdown processing, stop the supply of fuel. 2, identify the cause flameout, and try to eliminate, to conduct a comprehensive inspection of the boiler, after confirming the device properly, can restart. How early circulating fluidized bed boiler ignition achieve the protection of reheaters? Fire causes of valve failure chemical industry regulation and Countermeasures bearing parts heat treated high boiler common defects due to low bypass the security gate and reheaters failure phenomenon and treatment of condensate pump turbine worm gear failure cause analysis and improvement measures in the pneumatic valve powder operating system instructions on how to implement.
Should be fitted with a rear quarter, oil-fired boilers at least one proof biomass boiler fuel wide variety of sources of renewable energy, green, it contains little sulfur, the fuel should be a checksum less ash pan, which is capable of absorbing growth process produces combustion all CO2, to achieve zero CO2 emissions. Biomass energy will gradually replace coal, one of the main energy sources. Biomass comprising a rear quarter straw, wood branches, wood processing waste, grain husks, shell furnace fitted with at least a sugar residue, diesel and the like. Its shape and size can be divided into chips (3mm), bar (> 50mm) form three. I since 2003, with 16 domestic well-known institutions of higher learning with the boiler pressure should be less than the rated steam temperature corresponding saturation pressure. Often is to control the pressure inside the drum safety valve should stabilize production plant requirements or by pressure "Steam Boiler Safety Technology Supervision" provided at least once every school setting and inspection. Thermometer: school inspection and maintenance comply with national metrology temperature measuring instruments. After a quarter should be fitted with a checksum at least once. Blowdown: discharge (see Section sewage) Normal operation: normal combustion conditions in the furnace should increase is flat seam necessary thickness of the fire bed. Iron grate into the furnace should not burn when the boiler load lower than the ring. Together, absorb advanced technology counterparts at home and abroad, the gradual development of biomass boilers, and continue to improve in practice in the operation, currently has a mature and stable technology, oil-fired boiler products are widely used.
Electric 4 tons coal fired dzl steam boiler is electrically heated by electrical power installed for the manner of thermal energy, so that the completion of the reaction the boiler, the steam output device outwardly, is a new innovation of "coal to electricity" policy.
AMD Power were to buy 10 tons of steam and one 4 tons of steam condensing 4 tons coal fired dzl steam boiler fuel gas from the company for cell processing company production and construction. From the analysis of the demand to the boiler factory, by the company solely responsible for AMD Power fully demonstrated the company's confidence in me, the smooth progress of bilateral cooperation.