Say the existing boiler models on the market, then it is countless, but from the looks of it, there is a cylindrical, vertical, horizontal, etc., these are more common in older boiler room. And in some newly built boiler room, one Taiwan "modular" better known and boiler use.
How to maintain water supply and boiler water of Fangkuai boiler during operation the quality of water supply and furnace water of Fangkuai boiler should meet the requirements of GB/T1576-2008 (Industrial Boiler Water quality). And sample and test regularly. The quantity and frequency of the discharge shall be determined by the laboratory personnel. Test and discharge shall be recorded in detail. 2 Monitoring of rotating machinery shall be carried out by means of one look, two ears and three touches for pumps, fans, pumps, etc. The discovery of anomalies, that is, take measures to deal with. If necessary, the furnace should be shut down and overhauled, but it should not be careless. The oil level of the tank on the 3rd day If there is no automatic control device for oil level, the oil level should be checked regularly and it is found that the oil level is too low to be used for 2 hours. Please inform the fuel personnel in advance of the injection of new fuel. 4 the water level control of the soft water tank is generally used to automatically control the operation status of the 5 water treatment equipment to check periodically for the failure of ion exchangers in the water treatment equipment. Under normal conditions, the exhaust temperature of the new Fangkuai boiler is generally low, and will gradually increase with the increase of the running time. If it is found that the change is too large and exceeds 20 ℃, the appropriate time to shut down the furnace and clean the ash should be chosen. Such phenomena as If it happens frequently, check that the combustion system is normal. If the oil pressure is too low, the oil temperature is too low to atomize bad, or the air-oil ratio is not correct, resulting in bad oil-gas mixture, resulting in anoxic combustion and carbon precipitation. In addition, for dry-backed boilers, if the exhaust temperature increases abruptly, it is possible to leak smoke from the fire-proof wall between the second and the third return of the rear chamber, which needs to be repaired.
The purchase of gas-fired boiler, we are more anxious shopping center, but for gas-fired boilers are not very understanding. After the introduction of others, we understand each other fast boiler more comprehensive, and more trust fast boiler. After the boiler put into use, it turns out, party fast products fully meet the needs of our shopping centers. --customer feedback
After saving gas boiler also need to test it? In general, the boiler before being put into normal use, will be through the test to ensure normal operations of the respective other auxiliary elements; while ensuring smooth and safe operation of the overall state of the boiler. So, with the increasingly stringent national environmental policy, the transformation of the boiler has been steadily advancing over the country, it is also part of the boiler users, in order to save the drawing efficiency or other reasons, no longer boiler test, then, after what energy-saving gas-fired boiler also need to test it? in general terms whether it is a new boiler or after the transformation of the boiler before being put into regular use are required to test, and to do at least two advantages, boiler components and raw after the transformation necessary to ensure can be configured between organic combination boiler, ensure the transformation of boiler operating efficiency, stability, safety has improved. The second is to ensure timely corrective action process is in the process of debugging abnormal phenomenon, to avoid re-enter after normal use, causing unnecessary boiler accident. In short, after the energy-saving gas boiler, put on trial before use or necessary, must not for the easy way or the other reasons cause unnecessary trouble, not worth the candle.