Before a cooperation with the parties, we heard from other companies where fast 8 ton condensing low nitrogen coal boiler project brand, saying it was so fast square product quality, use a long time, and after-sales service is also very complete. After the collaboration found that it really is a well-deserved reputation. This three boilers put into use, not only reduces emissions, while meeting the needs of normal heating, fuel input has also been reduced, as we save a lot of operating costs. --customer feedback
Function of oil-fired 8 ton condensing low nitrogen coal boiler project furnaceThe furnace of oil-fired boiler, also called combustion chamber, is the space for fuel combustion. The furnace in which the solid fuel is placed on the grate is called a layer-burning furnace, which is also called a fire-bed furnace, and the liquid, gas or powdered solid fuel is injected into the furnace burning in the fire chamber, which is called a chamber-burning furnace, or a fire-chamber furnace, which is also called a fire-chamber furnace, which is called a chamber-burning furnace, or a fire-bed furnace. The furnace in which the coal particles are lifted up by air to burn in a boiling state and suitable for burning inferior fuels is called a boiling furnace, also called a fluidized bed furnace, and a cylindrical furnace in which coal particles are rotated at a high speed by air flow and burned intensively is called a cyclone furnace. The cross section of the furnace is generally square or rectangular. The fuel burns in the furnace to form flame and high-temperature flue gas, Therefore, the furnace wall around the furnace is composed of high temperature resistant materials and thermal insulation materials. Water-cooled wall tubes are often installed on the inner surface of the furnace wall, which not only protects the furnace wall from burnout, but also absorbs a large amount of flame and high-temperature flue gas in the design of the furnace, which needs to take fully into account the characteristics of the fuel used. Each boiler should burn the original fuel as far as possible. The economy and reliability of boiler operation may be reduced when the fuel with different characteristics is used.
Development condensing gas 8 ton condensing low nitrogen coal boiler projects What's the point: To reduce fog and haze, clean air environment, working across the country are carrying coal to gas boilers. The advantage of using gas-fired boiler coal-fired boiler, many alternative, the first gas itself clean, dust does not occur during transport and during use, and gas generated by the combustion of sulfur dioxide and nitrogen oxides are also less than in coal-fired boilers. The use of gas-fired boiler itself is in line with the needs of environmental protection, but the cost of natural gas than coal, so we must ensure that the use of gas-fired boiler thermal efficiency of boilers, condensing gas boiler was born!
Several factors underlie the vertical steam 8 ton condensing low nitrogen coal boiler project efficiency China has been working to catch on coal to natural gas, vertical steam boiler with greatly reduced contamination of dust, smoke and other effects of a nitric oxide gas has also been healthy curb. Efficiency is an important indicator of a measure of vertical steam boiler, a good number of factors under the topic to discuss the direct impact of vertical steam boiler efficiency began. After analysis of stakeholders, heat loss from vertical steam boiler contains two pieces: the proportion of full combustion air with flue gas emissions unreasonable heat loss. Heat loss can be reduced smoke emission can be installed at the end of the vertical steam boiler stack waste heat reuse install, or more leading system with condensing boiler. Combustion air ratio sufficient unreasonable faults into: general vertical ejector-type steam boiler burner selection, resulting in a motor fuel ratio can not be adjusted. Most of the selected vertical steam boiler is mechanically strong emission combustion engine, air-fuel ratio resulting irrational factors are the following: air-fuel ratio can be divided into two reasonable chance comprising: when the air in excess, the excess will have full cold It is heated, resulting in increased operating costs vertical steam boiler, steam boiler efficiency vertical drop; when the air is not enough, will produce insufficient burning phenomenon, caused by vertical steam boiler efficiency.