Daily care and maintenance of boiler equipment: As we all know, some companies steam boiler is used to provide large-scale steam equipment, production process more complicated and therefore, the steam boiler is an expensive business if long-term use, reduce the cost of steam boilers is. necessary to face the high price of boiler products, how to maintain?
As a leader in the fast side condensing gas boiler, in recent years, provide a clean boiler to Beijing multiple office units, was well received. I units through the preliminary investigation and contrast, select fast boiler, it turns out, party fast product does have quite a good cleaning environmental performance, in line with the Beijing municipal government requirements for air pollution emissions, the use of very at ease. --customer feedback
Gas boiler furnaces and cooking formal operation of the boiler furnace 1, and its object is to clear the body of the boiler impurities, grease and rust. The inspection of boiler installed and cold test run, each member confirms perfect safety conditions have hot start operation to start cooking stove. 2, boiling out dosage (see table below) Unit: kg / t rust grease Drug Name Notes thicker thin rust grease sodium hydroxide (NaOH) 2 ~ 33 ~ 4 trisodium phosphate (Na3PO412H2O) 2 ~ 33 ~ 4 when no trisodium phosphate, sodium carbonate can be used (of Na2CO3) in place of an amount of 3 to 6 kg / t water. 3, when dosing, the low water level in the boiler water should, boiler water should be the highest level, the drug was added on the stove interfaces (e.g., valve opening) when the cooking stove. 4, the end of the cook should the boiler furnace pressure was kept at about 75% of the working pressure, time is generally 2 to 3 days. 5, during the cooking stove, boiler water periodically take laboratory analysis, alkalinity boiler water of not less than 45 meq / L, should be added or dosing. 6, oven cooking is completed, the drum and the current tank should be cleaned precipitate, rinsing the boiler and in contact with the agent through a valve, to check whether or clogging sewage. 7, after cooling boiler, furnace water will be fully released. Open manholes, hand holes, repeatedly washed with water until the furnace no rust, grease qualified. (Ix) a test run, the test run should be with a load, for 4 to 24 hours (set maximum, minimum operating pressure). 2, observe the safety valve and various safety accessories, protective devices and other operations are sensitive and reliable. 3, after the commissioning of qualified, supervisory inspection agency should be acceptance.
Prevent gas boiler explosion focus is that all three at the same time not to reach a certain limit. Among them, air is everywhere, to get rid of this condition is very difficult, so the focus is concentrated in the explosion on the gas and heat. So, at this stage almost all of the gas explosion-proof technology has focused on how to deal with gas and heat.