Gas-fired how to start fbc boiler installation Note: Many users in the purchase of gas-fired boiler for the needs of the product itself, faced with the installation of the boiler. According to Xiao Bian experience fast boiler technician for many years at the user site installation of the boiler, summed up the following gas-fired boiler installation considerations, hoping to help your boiler installation go more smoothly. 1, to determine the installation site of the boiler, the boiler units installed must have a certificate installed boiler installation requirements issued by the higher authorities. 2, for registration, in accordance with "Steam Boiler Safety Supervision", the use of boiler units need to check in on each boiler. Boiler units need to have someone in charge of the work, is responsible for the communication with local pot seized, butt all installation procedures. 3, check the boiler and accessories for boiler combustion equipment, auxiliary components to conduct a comprehensive inspection and acceptance, and make a record, if found non-compliant parts in a timely manner to reflect to the boiler manufacturers. 1, boiler, auxiliary equipment, accessory boxes, meter boxes etc. need to be hoisting the specified location, location not be changed. 2, around the mounting location should allow sufficient space to facilitate post simple maintenance, boiler doors and various inspection hole to ensure that open. 3, the boiler room, it is necessary to leave the air inlet, but also with filters and other apparatus, and cleaned, to prevent clogging. 4, the boiler room can not be placed flammable flammable material, highly corrosive gases and volatiles. Third, after the completion of the installation inspection. 1, after the successful landing of boiler installation, you also need to conduct a comprehensive inspection and maintenance work, ensure that the boiler will not flaws in the post-investment runtime.
20tph SZL series coal-fired water tube how to start fbc boiler project for textile industrySteam boilers are used to provide sufficient steam in drying, knurling, sizing and other production process of textile industry. Kay & Emms (Pvt.) Ltd., headquartered in Pakistan, is one of the leading manufacturer and exporter of quality garments and fabrics. With the development of the company, the total amount of steam produced by their boilers in service can not meet the production requirements. Therefore, Kay & Emms (Pvt.) Ltd. made a decision to book several efficient steam boilers. ZOZEN has had rich experience in Pakistani textile industry and already gained the favor of many well-known enterprises. Kay & Emms (Pvt.) Ltd. also chose to partner with ZOZEN without any hesitation. In consideration of the urgent demand for their production, sales manager from ZOZEN recommended 20tph SZL series water tube steam boilers to the company. The series of steam boilers are not only designed to be shop-assembled type, which features compact design, convenient field installation and short production period, but also equipped with advanced control system for easy operation. Meanwhile, the performance and emissions have also achieved the international standard.
If used in some bathing establishments how to start fbc boiler, when the boiler water shortage emergency, instant evaporation of water, boiler dramatic expansion in a short time. If this is really explode up, 20 meters away could be hit brick or something like that, endanger within a radius of 10 meters.
This year, located in Guizhou Tongzi County and located in Heilongjiang Harbin has two how to start fbc boiler explosions accident, after investigation, the accident was produced in the installation link, there are companies the main responsibility for the implementation of incomplete installation link, confusion installation and construction management , unauthorized commissioning, pressure testing irregularities, installation supervision and inspection to ensure the role of the missing and other problems, leading to a boiler explosion occurs, causing adverse effects for the personal and property safety.
Market supervision bureau to draw lessons from the accident, in order to avoid explosion due to boiler installation problem from occurring again, issued a notice warning of the risk of boiler installation link. Details are as follows:
The boiler safety related technical specifications, the entire boiler manufacturing unit can be installed (set) mounted boiler units produced. Boiler manufacturing unit undertake installation work, should meet the following requirements:
The manufacturer should be dedicated departments boiler installation work, set up to cover the boiler installation quality management system, equipped with the necessary resources to installation conditions. Boiler manufacturing units should strengthen sales management, through specified in the sales contract if the terms of the unit responsible for the installation of boilers, etc., to prevent sales by the manufacturing license qualification units or organizations which are not allowed to undertake the unit personnel to carry out boiler installation work. Where specified in the contract manufacturing sales unit responsible for the installation, on-site installation work must be sent by the company to complete the installation personnel shall not be subcontracted to other units (safety specifications are allowed in the assigned project except). Indicate the sales contract to this unit responsible for the installation of the boiler, installation of the unit must have the appropriate license installed. Responsible for the installation of the units should strengthen safety education and skills training for installation personnel. Find that the installation quality and safety aspects of the occurrence of an accident or appears illegal activities, special equipment safety supervision institutions should be punished according to the law to install the unit.
Boiler installation units should strictly enforce the relevant safety standards and technical specifications to ensure the quality and safety of boiler installation, the unit should be installed at the installation site set up signs stating the name of the license holder of the certificate, license project, license number and items the person in charge, who is responsible for safety and quality, commissioning personnel, supervisory inspector's name, unit and telephone. Boiler commissioning and commissioning, operation must be performed by a licensed boiler operator. Before the boiler installation, inspection and acceptance by the relevant formally delivered, installed units should be hung in a prominent position boilers warning signs with the words "banned" and take effective protection and quarantine measures to ensure that the boiler system can not be ignited or boost . In addition to the need to debug, the cabinet can not be energized, the fuel valve is in a closed state should be like. Use blanking panels of the boiler pressure test, the test should be removed immediately after the end of the Blind.
Boiler boiler installation situation before construction units should be installed by informing the local special equipment safety supervision and management departments, and submit an application to install Supervision, Inspection and supervisory inspection agency. Where Supervision and Inspection uncommitted boiler installation project may not start.
Supervisory inspection agency should be strictly in accordance with the "Boiler Inspection Rules", according to the supervisory inspection protocol and progress of the project requirements, arrangements for the implementation of the supervisory inspector boiler installation supervisory inspection. A class of control points, the supervisory inspector must be at the scene confirmed to meet the requirements, the installation unit in order to continue with the work. Supervisory inspector shall, at the start that is to the construction site, in the whole process of site supervision to pressure test, shall not be used after the witness confirmed that and how do fill supervisory inspection program Supervision, Inspection and replacement process when the boiler pressure test.
Boiler manufacturing unit in particular is responsible for boiler installation of manufacturing units and boiler installation supervisory inspection agency, should an accident lessons learned, giving top priority to further implement the main responsibility and checks responsibility, strengthen the boiler installation management to ensure the quality of the installation work, protect the boiler safety.