Which improve the efficiency of two coal-fired heating heating system (ie factory reasonable diesel boiler price efficiency and network transmission efficiency) is the key to energy conservation, and in strict accordance with the relevant points to achieve rational use of machinery and equipment for better efficiency measures szs boilers have heating effect and improve equipment operating efficiency, and more reliable consumers want to improve the efficiency of heating boilers Shenzhen should also follow this principle. (1) improve the efficiency of the boiler szs. Rated efficiency of the boiler thermal efficiency of the boiler is not just the individual, but the seasonal efficiency of the boiler. In order to improve the seasonal efficiency of the boiler, should be reduced as much as possible to start SZS boiler heating period, down time and standby time. But this is because every time by clearing the speed of boilers, boiler stop calorie consumption, standby time is the heat sink can cause considerable damage. In order to improve the seasonal efficiency of the boiler unit, select the type of boiler it is very important. When choosing the type of the boiler, the boiler must consider how a variable load combination has a better ability to regulate, and how to improve the minimum output of the boiler to match the smallest possible load. (2) improve the transmission efficiency of the network. Factors Affecting SZS network transmission efficiency boiler there are three, i.e., heat loss insulation, heat losses and leakage of heat loss caused by the hydraulic disorder, wherein the heating system heat losses and the level of external network unbalance unbalance vertical heat loss very serious. Boiler pipe network outside the level of imbalance and indoor heating systems is the loss of a large vertical imbalance in the ratio of heat so I want to improve boiler efficiency must improve the efficiency of network transmission Shenzhen. At present, higher energy costs, thus reducing the boiler heat loss network is very important. In order to reduce heat transport pipe network losses, SZS boiler hydraulic balance system should be used, and temperature control system.
July 26, 2016, Beijing, China Everbright Paper Co., Ltd. and the company signed a "split 6 tons of steam condensing gas steam factory reasonable diesel boiler price contract" by the company responsible for the WNS6-1.25-YQ split condensing gas boiler steam to all production, installation and commissioning work. The product is the use of condensing technology, effective emission of harmful substances SOx, NOx, COx, is industrial boilers efficient and environmentally friendly solutions.
How to determine dry steam factory reasonable diesel boiler price apparatus generates an accident when the minimum water level height inferior already defined, but is still able to see the water meter water height, is slightly less water; see count was observed when the water level of water is less than the height, severe lack of water. Status summarized as follows: (1) conventional water drum water height inferior to the height defined; (2) low level alarm, sound warning devices, flash lights from; (3) the temperature of superheated steam to improve the water vapor; (4) does not enter a conventional water , less than the amount of steam; (5) steam temperature increase smoke emissions.
SZS series horizontal factory reasonable diesel boiler price is in D type arrangement, there is a burner in front of the furnace, so the effective area of the furnace are increased. Before high temperature gas is emitted through the chimney into the air from the economizer, they will loop through the furnace , over-heater, convection bank. The circulating in the convection bank between the upper and lower drum are belong to natural circulation, It is typical and high reliability natural water circulating structure, have high self-compensation, automatic allocation feature for ratio of rise and fall, so the water circulating is reliable and safety. And the convection bank also immensely increase the heating area, the economizer is protected by it because water in the convection bank Absorbed more thermal, the temperature of the gas through the economizer is lower. This is the reason for the horizontal boiler with overload.