What kind of pressure gas distributor 2t fired boiler quality no good people bought gas pressure boiler, even gas boiler no contact with people, has been more emphasis on the market in gas boiler election time, in the selection of the boiler, the name suggests is designed pressurized gas boiler category, this means, electric boilers, gas boilers and good use of comparative advantage is up relatively well. First of all, pay attention to safety regulations, gas boiler should pay attention to the use of safe fuel, electricity; In contrast, the general election need to reduce the number of gas-fired boilers for gas requirements of sensitive issues, a lot of energy, design issues become more complex, selected gas boiler, pay attention to certain parameters is a relatively routine procedure. In view of the use of the burner, the air supply system is the best embodiment of the gas boiler, the air supply system, must pay attention to air flow, air and other details, particularly in the light housing, the motor and the associated wheel, excellent results Therefore, when using gas-fired boiler, the overall effect of highlighting the advantages of maturity is a very sensitive topic. In the detection system perspective, the use of pressurized gas boiler is based on the practical effect of the above, to ensure the safety of the gas, pay attention to the ability to run the election is now the basis of the performance of gas-fired boiler, fuel system, and even the electronic control system , becoming the selected gas boiler, note controller uses a set of programs, large LCD screen, security control is inevitable.
Recently, the Longhai carried out safety campaigns to the distributor 2t fired boiler, the campaigns start from the four directions, whether units in accordance with the boiler 'boiler safety practices "to use the correct boiler conducted a comprehensive inspection.
First, the unit register in a boiler boiler inspection. The use of units to crack down on unauthorized use of untested or failed the inspection of boilers.
Second, the units are equipped with a boiler if the security officer and fireman personnel. Focus on checking whether the use of units as required "special equipment operator assessment rules," the fireman with security personnel and staff to meet the requirements, and whether the person has made fireman fireman card.
Third, in the boiler unit will be the safety management system, emergency plans to check the system; and to convey the importance of this inspection in the boiler unit, raise awareness of security units.
Fourth, strengthen supervision of energy-efficient boilers, boiler and actively promote energy efficiency testing, at present, boiler energy efficiency testing has been completed a total of 112 units.
To date, the Longhai inspection operations were dispatched inspectors 209 passengers, checked boiler unit 136, check the boiler 168 units, eliminate safety hazards at 9, and urge the use of sealed units to enhance the energy efficiency of boilers 21 units.
And with the Commission by letter, and environmental protection departments to further promote the comprehensive upgrade of coal-fired boiler energy saving project, disable the coal-fired boiler 53 units, 34 units scrapped, replaced by raw material boiler fuel and natural gas fuel of a total of 40 units, is out of the city coal-fired boilers to make a positive response.
With the increase of air supply volume, the mixture of oil mist and air is improved, which is beneficial to combustion. However, if the air volume is too large, the furnace temperature will be decreased and the incomplete combustion loss will be increased. At the same time, the heat loss of exhaust gas will be increased and the power consumption of the fan will be increased because of the increase of flue gas. If the air volume is insufficient, the combustion will be incomplete, resulting in carbon deposition at the tail, which is prone to secondary combustion accidents. Therefore, each distributor 2t fired boiler should pass the thermal efficiency test to determine its economic air volume at different loads. In practice, the stoves usually take into account the ignition of the nozzle and the carbon dioxide or oxygen content in the flue gas. Content to adjust the supply air volume. If it is found that the combustion condition of a nozzle is not good, or if the atomization plate with different aperture is replaced, the air pressure of the supply duct should be kept unchanged, and the opening degree of the duct baffle of the nozzle should be adjusted to normal combustion. If the fuel quantity changes due to the change of the oil pressure in front of the furnace, the opening of the fan baffle should be adjusted to achieve normal combustion by changing the air pressure and air volume of the air supply duct when it is necessary to adjust the supply air volume.
3) the observation and analysis of all kinds of flame when adjusting the fuel oil. Generally through the fire point adjustment and flame center adjustment to complete the flame adjustment. The ignition point of the oil mist should be close to the nozzle, but there should be no tempering. Early ignition is beneficial to complete combustion and stability of oil mist. However, the fire is too early, too close to the nozzle, easy to burn the nozzle and furnace wall to determine the mouth. Furnace temperature flying oil varieties and atomization quality, as well as air volume, wind speed and oil temperature, will affect the distance and proximity of the ignition point. So if you want to adjust the ignition point, you should find out the cause in advance, and then take targeted measures. When the boiler load is constant and the oil pressure and oil temperature are stable, Should be based on the ignition point wind speed and wind distribution situation.
Established in year 1945, ZG is a manufacturer and international trader specialized in the research, development and production of Power Plant distributor 2t fired boiler and Spare Part; Gas fired boiler; biomass fired boiler . We have rich experience to help power plant owner to solve all kinds of power plant boiler problem.