Fan about n2 blanketing in thermal boiler uses coal boiler using a mechanical energy to heat, then the boiler must use such equipment in the ventilator during use. Today, we are concerned that the role of the fan in the boiler. Boiler fan is chosen depending on the model and specifications of the boiler in the selection, but fans can also play two different roles in this area, but on the principle that ventilation is still the same. Device for conveying air into the boiler is fan. If you want to use coal for greater efficiency in the boiler, we need more oxygen. Since the boiler is in the shape of a hermetic shape, it is not possible to allow the air to the boiler initiative complete combustion. This time we should use the power boiler fan, the air supplied to the boiler which mechanically energy, in order to make coal in the boiler more complete combustion to provide more heat.
CFB steam Boiler to produce electricity for industrial usage
Such as hotel Home Hotel Group is one of the three major brands, in 300 cities in the country has nearly 2,000 hotels. Home Inns has won China Golden Pillow Award for Best Chinese economy hotel chain brand award, in 2014, Home Inns brand value of $ 420 million of selected China's top 100 brands. April 4, 2016, BTG hotel groups such as the privatization of the hotel purchase transaction has been completed delivery. In mid-2016, as a Beijing hotel with our preliminary communication, the urgent need two about n2 blanketing in thermal boilers work of heating and hot water supply. I related technical engineers and recommend it to calculate the number and size of the boiler on the hotel room as hotel Willy sharp V6-99 two models.
The reason the change in vapor pressure of the about n2 blanketing in thermal boiler boiler operation could lead to vapor pressure change actually reflects the balance between evaporation boiler load changes with the outside world. It causes changes in two main areas: (1) outside interference. That is, changes in the external load caused by steam pressure changes. When the evaporation boiler below the external load, i.e., sudden increase in the external load, the vapor pressure is lowered, when the external load is just to meet the evaporation, vapor pressure and to maintain normal stability. (2) interference. Changes in working conditions within the boiler is caused by steam pressure changes. The combustion conditions change, the change in the fuel properties, fire mouth of start and stop, start and stop or blockage pulverizing system, furnace fouling, coking, coal and air ratio changes and the fouling effect of thermal exchange or the heating surface tubes leaks, burst pipes and so will the vapor pressure changes occur.