Rubber Vulcanizing need high temperature steam, while steam generation is produced by steam boiler. In rubber industry, steam boiler play an important role which supply high temperature steam. Steam boiler fuel can be: Rice Husk, Coal, Lignite, Washery Rejects, Char, Indian/Imported Coal, Petcoke, Pith, Wood etc. Boiler prices for steam generation in rubber industry, please contact our online service, and we need to comfirm the capacity, pressure, temperature.
Inter-regional Pingdingshan Coal Industry Group Co., Ltd. by the Pingdingshan Shenma Group and two Chinese top 500 enterprises founded by restructuring, cross-industry, cross-ownership and transnational business of large state-owned energy and chemical group, under the People's Government of Henan Province , is the most complete variety of coking coal, thermal coal production base, has Asia's largest chemical production base in nylon. Carefully selected and comparison, fast boiler Pingmei cooperation with party has chosen to provide a 2 tons of steam electric dzl2 1.25 aii coal fired 2 ton steam boiler to tanzania (WDR2.0-1.25-II) by a fast side.
Main dzl2 1.25 aii coal fired 2 ton steam boiler to tanzania temperature abnormal phenomenon of how to do 1, main steam temperature anomalies alarm. 2, the rapid variation of the main steam temperature, a secondary damper frequently significantly reducing water operation. 3, starting superheat outlet steam separator above or below normal. 4, if the steam with water, the unit will water shock occurs. 1 reason, the fuel and water supply imbalance, the separator outlet temperature abnormality. 2, coal combustion conditions change or affect, such as excessive load lift; and pulverizing mill administration system abnormality stop; means automatically increase or decrease the failure rate is too large amount of wind and the like. 3, the central flame furnace changes, such as the bottom seal damage, W and inadequate flame downstroke. 4, the control failure by warm water, warm water flow rate reduction is abnormally reduced or increased. 5, feedwater temperature mutation. 6, does not match the wind coal. 7, the secondary combustion heating surface. 8, furnace coking or fouling seriously. 9, heating surface leakage squib. 10, flue gas damper opening degree is not normal. 11, coal sudden change occurred. 12, the uniformity of the powder feeding substantial change occurs. 1 process, failure caused by unit coordinated coal - water ratio should be immediately released coordinate offset, in accordance with the current load demand, with reference to the start of the steam superheat separator, and adjusting the amount of fuel corresponding to the amount of water, with one, two main desuperheating water rapidly steam temperature control in a normal range; when the coal - water ratio should avoid imbalance after coal and water while adjusting; when coal - water ratio is adjusted to further adjust the load after a relatively stable; contact maintenance processing timely. 2, when the water supply system fault condition occurs a significant disturbance furnace should pay attention and automatically coordinated working conditions, so as not to manual intervention, when not working properly coordinated and automated, should be manually adjusted, stable water flow, referring to separation according to the water flow steam superheat, the adjusted amount of fuel, with a secondary spray water rapidly controlling the main steam temperature within the normal range; contact maintenance processing timely. 3, due to rapid changes in load caused by the load change rate should be adjusted; load change caused due to protective operation or the like caused by heat load to be quickly adjusted to maintain the boiler pressure of the main steam stability. 4, by warm water automatic dysregulation, should be appropriate Save warm tone is switched to the manual may be an intermediate point of the feedwater control system be corrected for temperature if necessary, or the feedwater to switch control to manual control, due to lower lifting and lowering the load speed to prevent steam temperature, promptly contact a service process. 5, the boiler furnace cause severe fouling and coking of the main steam temperature anomalies can be corrected by an appropriate degree of superheat outlet steam separator start, adjust, and in a timely manner and the furnace heating surface sootblowing. When the platen superheater sootblowing or superheater outlet temperature is still above normal and a secondary reducing water damper fully open, to check the furnace and the combustion air distribution system is normal, the checking process to reduce still overtemperature unit load. 6, flue gas damper adjusted to an appropriate opening degree. 7, if the bottom seal after losing back to normal immediately. 8, to strengthen the turbine expansion, differential expansion, axial displacement of the shaft vibration and bearing temperature monitoring, if abnormal, the process according to the corresponding regulations. 9, after the above measures, if invalid, should immediately drop the load process. 10, in front of the main steam temperature main steam 50 ℃ drastically reduced within 10 minutes, should an emergency stop.
After the gas hot water boiler hot water boiler vaporization emergency 1. Vaporization handler circulating pump stops abnormally pump failure caused by: ① blower stops running immediately. ② immediately open the door, take measures to pressure the fire, lift the chute gate, cutting off the supply of coal grate. ③ In the case of boiler pressure not greater than 0.6MPa (600KPa), the exhaust valve to follow, only a sharp rise in pressure in the boiler deflated, used only relief exceeds 0.9MPa, and the exhaust process to be carried out slowly, prevention boiler due to loss of pressure and more violently again vaporized. ④ close the boiler water, water main gas valve. ⑤ open stop valve recirculation line, to ensure that the water supply pipe velocity convection heating surface (economizer) to prevent re-vaporization of the economizer. ⑥ The operation of the above operation, at the same time to pay the boiler to reduce the boiler water temperature and the furnace pressure. ⑦ After the boiler pressure is normal, i.e., opening the standby circulating pump, into the normal combustion. 2. Treatment failure or sudden loss of power boiler vaporization of power: ① immediately open the door, lift the coal chute slide gate to take pressure fire measures to reduce the oven temperature. ② Grate with the fastest speed in order in the shortest time to fire onto the slag tap. ③ the degree of treatment in the first case. Once a short time can not supply heating network system, antifreeze should take emergency measures. 3. Due to excessive heat boiler boiler vaporization process: ① the immediate closure of the drum, induced draft fan. ② immediately open the door, take measures to pressure the fire, lift the supply of coal chute slide gate, off of coal, while the grate into fast gear. ③ In the case confirmed the presence of water, the boiler can supply water to the boiler body, boiler out of the water while closing the main valve. ④ Open line stop valve recirculation pump to ensure water velocity convection heating surface of the pipe, to prevent the economizer again vaporized. ⑤ Open circulating pump with jog mode, jog each time less than 30 seconds, again less than one minute jog interval. Jog purpose is to reduce the boiler water temperature, while preventing a large amount of steam into the pipeline system. ⑥ back into place after the safety valve, circulating pump running, and then the normal burning stove. 4. Water boiler system run vaporization process due to water loss, loss of pressure caused by: ① immediately closed drum, induced draft fan. ② out of the water while closing the main valve and the boiler circulating pump. ③ take the same measures to cool the furnace tube described above. ④ Open stop valve recirculation line. ⑤ rely exhaust valve until the safety valve back into place. ⑥ until the boiler water temperature drops below 50 ℃, when the temperature of the furnace temperature less number 200 ℃, again within the boiler feed water, water course to be carried out slowly, to prevent harm to the boiler when the temperature is too large. ⑦ After processing leakage fault, the system time to the replenishment, and out of the water boiler always open the valve, and the circulating pump, and then normal combustion.