The contract is valued over €15 million and is set to be completed by the end of 2015. ZG will deliver one 135 MW steam turbine, with generator set and auxiliaries, including the water-cooled condenser for the coal-fired power plant.
ZG is one of biggest internal CFB 98 efficiency mini electric steam generator manufacturer in China, The internal CFB Boilers plants provided in a successful operation for many years in capacities ranging from 30 to 350 MWe. Steam generators with internal circulating fluidized bed (ICFB) combustion have found acceptance throughout the world over the past few years, in particular for power generation, but also as industrial CFB power plants and cogeneration CHP stations.
Battle blue horn sounded, emissions of sulfur, nitrogen and oxygen compounds gradually strict national requirements. To improve the quality of the environment, but also the people a blue sky, in all industries around the environmentally friendly product revolution, Hainan Sinochem Pharmaceutical companies are no exception. By the company investigation and comparison of 98 efficiency mini electric steam generator products, in March 2017 signed a six-ton steam-cleaning integrated condensing gas boiler and steam fast boiler. Tested and post feedback, the boiler equipment installation qualification, operating normally, and successfully passed the inspection by local quality inspection departments of the boiler.
Heating 98 efficiency mini electric steam generators partial failure of boiler pressure controller controls the generator, because there is no water showed no the control circuit board, which is mainly controlled by heating the liquid level control float. When an appropriate amount of water, floating on control splendidly floating-point voltage, so that the boiler applied AC contactor work, start heating. This simple structure generator, the current market use more circulation. Such a generator common fault is not heated, mostly appear on the float level controller. First check the external wiring float level controller, whether the control point of the vertical line connected pair, and then split the float level controller, to see if it floats flexible. Then you can use the manual, the heat upper and lower part of the fault can be turned on by the control point whether the amount of the multimeter. After checking everything is normal, then check whether the water tank float. In other words it can float, i.e. the fault is rectified.