Stanley Agricultural Group Co., Ltd. is specialized in the production and sale of fertilizer and other agricultural technology promotion of integrated services provider, has total assets of 6.3 billion yuan, more than 8,000 employees, annual production capacity of 5.2 million tons. Earlier this year, fast Boiler stand out in many boiler manufacturer in aurangabad brand competition, and Stanley reached a cooperation, to provide a whole 10 tons of steam condensing steam boiler (WNS10-1.25-Y.Q), provide support for the heat Stanley fertilizer plant.
According to the local conditions, the boiler use unit formulates the relationship between the boiler outlet water temperature and the outdoor air temperature. In the operation, according to the corresponding relationship between the specified outlet water temperature and the outdoor air temperature, the combustion amount is adjusted in time, and the water supply temperature of the network management system is required to be different from the specified temperature. 120 ° C. The change of water supply temperature should be carried out step by step, and the water temperature increase or decrease should not exceed 20 °C.
Boilers and furnaces distinction and deaerator Optional: heat transfer station and the boiler manufacturer in aurangabad room, the difference between them, what is? Optional deaerator on the boilers, which usually is? And, boilers and furnaces distinguish between simple right? These issues are on the boiler, and that is very important and basic, so below, immediately give a specific answer, so that we learn through to clear, rather than a smattering. 1. heat transfer stations and boiler room, the difference between them is mainly what? The difference between the boiler room and the heat transfer station, if summarizing, then, there are mainly the following, is: one difference: heat transfer station, which is to convert the boiler room to the production of hot water a user may direct use of hot water, its temperature is lower than 100 degrees Celsius. And high temperature hot water generated by the boiler room, is higher than 100 degrees Celsius. Difference between the two: the boiler room for the production, the heat transfer station is as a transit station, so they used the device, is not the same, that can not be mixed. 2. Optional boiler deaerator, should be how to choose? Deaerator, which has a head type and there is no points of the first type. In the boiler, which is typically the first type of this kind of choose, without selecting the type of this kind without a head. However, if it is a large boiler plants, because it is more than 1000t / h, then, it is to adopt non-tower-type deaerator in order to meet the demand. And, on this point, we should have a clear understanding, you can not go wrong.
Mostly used in the membrane wall water tube boiler manufacturer in aurangabad, having a simple structure, save steel, insulation and air tightness better advantages.