Gas Steam Boiler non-normal stall, a phenomenon and treatment, flame reasons: 1, the operation of the auxiliary power supply or trip interruption. 2, boiler combustion instability. 3, the load is too low, so that the load sharply mill automatic ignition energy loss or failure of combustion. 4, mutant coal, coal volatile or low calorific value. 5, the automatic combustion flame detector failure or failure caused by tripping mill. 6, or blast furnace wall tubes serious improper boiler soot-blowing operation, a large amount of water vapor into the combustion chamber. 7, coal pulverizing system, fuel system failure, resulting in a significant amount of fuel reduction or interruption. Or with a large amount of water in the fuel oil gun blocked too many impurities, low pressure steam or atomized. Second, the phenomenon: 1, a significant increase in furnace pressure, furnace flame monitoring flameless CRT display. See the fire no fire hole, BTG warning window MFT warning lights. 2, the unit load decrease, the steam flow drops rapidly, each segment working medium temperature, the vapor pressure decreases, the value of oxygen surge. Third, the method of treatment: 1, if the MFT tripping protection, should an emergency shutdown processing, stop the supply of fuel. 2, identify the cause flameout, and try to eliminate, to conduct a comprehensive inspection of the boiler, after confirming the device properly, can restart. How early circulating fluidized bed boiler ignition achieve the protection of reheaters? Fire causes of valve failure chemical industry regulation and Countermeasures bearing parts heat treated high boiler common defects due to low bypass the security gate and reheaters failure phenomenon and treatment of condensate pump turbine worm gear failure cause analysis and improvement measures in the pneumatic valve powder operating system instructions on how to implement.
6 tons adjusting a combustion gas good quality low pressure coal fired steam boiler price for sale, normal combustion boiler three basic aspects of indicators include a uniform supply of the fuel, reasonable ventilation, adjustment the combustion. 1, to maintain the high temperature of the combustion chamber temperature of the upper layer is preferably in the 1100 ~ 1300 ℃, flame orange in color. Flame reddish color indicates that the amount is not enough to the wind, the color white indicates that excessive wind. It should be appropriately adjusted. 2, fuel ash to reduce ash content in the combustibles to be below 10%. 3, reducing the temperature of the boiler flue gas exhaust gas temperature should be controlled below 200 ℃. 4, holding furnace negative excess air boiler is 1.2 to 1.4, by adjusting the balance of the blowers to maintain the furnace pressure is -20 ~ -30Pa. 5, the thermal efficiency of the boiler to improve the thermal efficiency of the boiler should be kept above 60%. II. Combustion Adjustment 1, the amount of fuel to air required for combustion and the amount of a reasonable distribution. Ventilation should first increase the amount of fuel increases, it should first reduce the amount of fuel supply reduced ventilation. 2, the thickness of the seam and seam thickness configuration grate speed is 80 ~ 120mm grate speed at high, middle and low profile configuration of several commonly used methods:. 9a rapid combustion of thin seam b c thick seam in low combustion. 3 thick seam combustion speed, the segment with the wind blowing principle: burn promoting intermediate ends. That is, after the coal into the coal starts to warm up the shutter, fire line front arch, the primary combustion zone, the middle grate to burn the rear grate zone. Normal combustion conditions are: fuel from the coal at the beginning of the fire shutter 300mm, uniform flames, the fire bed formation, at the end of combustion from the end of the grate 300 ~ 500mm. 4. maintain proper furnace temperature to avoid coking. The fire bed to maintain the homogeneous combustion, to avoid burning fire bed obliquely. 6. The residence time of the fuel on the grate in less than 30 minutes.
Fangkuai Group has more than 60 independent intellectual property rights, advanced clean fuel boiler manufacturing technology, and jointly established a clean fuel boiler production, research and research cooperation base with Tsinghua University and Xi'an Jiaotong University. An enterprise with a R & D and test center for clean fuel boilers. The thermal efficiency of “Fangkuai” boilers can reach 107%, which has been included in the national special equipment energy-saving catalog. The company developed ultra-low nitrogen full premixed combustion condensing boilers and ultra low nitrogen emission fuel gas boilers, which are developed by the company using Ultran condensation technology.
Coal to natural gas operations bunch of factors that vertical pressure good quality low pressure coal fired steam boiler price for sale energy consumption indicators of the country are carried out in a big way, the choice of vertical steam boiler, to a large extent minus the pollution of powder, together with nitrogen oxides and other dangerous gases the press has been discharged. Energy consumption indicators is an important rule to measure vertical steam boiler, to discuss the next bunch of factors under pressure vertical steam boiler energy consumption indicators. By analyzing the relevant departments, vertical steam boiler heat loss occurs mainly includes two aspects: the proportion of non-standard sufficient combustion air with exhaust heat loss. Weaken the heat loss can be retrofitted in the vertical steam boiler chimney terminal latent heat of re-use form, or in the selection of better boiler system FGR. Combustion air ratio is not sufficiently decomposed inappropriate criteria: ordinary vertical ejector-type steam boiler burner based, air-fuel ratio can not be formed in the active mobilization. More vertical steam boiler based on a mechanical blower burner, air-fuel ratio due to the following standards several factors: air-fuel ratio standard comprises two situations: when oxygen is excessive, the excess will be an infinite cryogenic air by heat conduction, caused by rising energy vertical steam boilers, low energy consumption vertical steam boiler index; when there is insufficient oxygen, there will not be sufficient to ignite the situation, leading to low energy consumption indicators vertical steam boiler.