Oil and gas boilers appeared late, and oil was first used in boilers in the 1930s, when it was used as an auxiliary fuel in coal-fired chain grate boilers. Due to the poor quality of the combustion technology and the fuel at the time, accidents in which the fuel suddenly extinguished during combustion often occurred, and thus were not actually used.
6 tons adjusting a combustion gas steam 10 ton boiler, normal combustion boiler three basic aspects of indicators include a uniform supply of the fuel, reasonable ventilation, adjustment the combustion. 1, to maintain the high temperature of the combustion chamber temperature of the upper layer is preferably in the 1100 ~ 1300 ℃, flame orange in color. Flame reddish color indicates that the amount is not enough to the wind, the color white indicates that excessive wind. It should be appropriately adjusted. 2, fuel ash to reduce ash content in the combustibles to be below 10%. 3, reducing the temperature of the boiler flue gas exhaust gas temperature should be controlled below 200 ℃. 4, holding furnace negative excess air boiler is 1.2 to 1.4, by adjusting the balance of the blowers to maintain the furnace pressure is -20 ~ -30Pa. 5, the thermal efficiency of the boiler to improve the thermal efficiency of the boiler should be kept above 60%. II. Combustion Adjustment 1, the amount of fuel to air required for combustion and the amount of a reasonable distribution. Ventilation should first increase the amount of fuel increases, it should first reduce the amount of fuel supply reduced ventilation. 2, the thickness of the seam and seam thickness configuration grate speed is 80 ~ 120mm grate speed at high, middle and low profile configuration of several commonly used methods:. 9a rapid combustion of thin seam b c thick seam in low combustion. 3 thick seam combustion speed, the segment with the wind blowing principle: burn promoting intermediate ends. That is, after the coal into the coal starts to warm up the shutter, fire line front arch, the primary combustion zone, the middle grate to burn the rear grate zone. Normal combustion conditions are: fuel from the coal at the beginning of the fire shutter 300mm, uniform flames, the fire bed formation, at the end of combustion from the end of the grate 300 ~ 500mm. 4. maintain proper furnace temperature to avoid coking. The fire bed to maintain the homogeneous combustion, to avoid burning fire bed obliquely. 6. The residence time of the fuel on the grate in less than 30 minutes.
Horizontal oil gas fired 10 ton boiler in Greece is a horizontal style three pass fire tube boiler with oil, diesel oil, light oil, heavy oil, natural gas, city gas, LPG gas as combustion fuel. ZG Boiler is a prominent and professional industrial boilers manufacturer with Class A Boiler design and manufacture license since 1945 and we own rich experience, high quality, advanced technology and excellent service to meet customers’ demand.
Hot water 10 ton boiler is the essential equipment of our hotel, one of the parties to provide fast condensing pressure hot water boiler immediate operational effect. Our demand for environmentally friendly and out of the hotel itself, very high environmental performance requirements for boilers, party fast products fully meet our needs, the index after testing are in line with the relevant provisions of the State; with the outside atmospheric pressure remains stable sufficiently improved security index boiler, eliminating our worries. --customer feedback