Our business-to-steam boiler components produces steam attaches great importance to the quality of good or bad, it will indirectly determine the quality of our food is produced dates. The fact that we choose fast boiler is correct. We are very grateful to our fast boiler manufacturing plant in a short time, installation and commissioning of these two steam boilers, advance our production line went into operation. --customer feedback
Main steam temperature in the boiler components when a hot start is less than the rated Why? Hot Start For the boiler itself, in fact, is to a certain stage of the whole process of Cold Start as a starting point. When the unit stopped running, the boiler cooling faster than the turbine. If the turbine is in a semi-hot or warm, cold boiler may already start operation of such boilers essentially as cold to warm, boosting, to try to meet the red hot state turbine revolutions required parameters for input large amount of fuel, but this time only by the amount of the bypass system and a steam exhaust air is not enough, so that the steam temperature rises rapidly, and the walls and high temperature. Also, because the combustion chamber and the flue outlet larger width, uneven temperature distribution in the furnace, the superheater tubes are not circle the steam flow rate, the temperature difference is large, causing local over-temperature superheater tubes. To prevent over-temperature superheater, extending its life, so to start the predetermined process in the main steam temperature should be lower than the rated 50 ~ 60 ℃.
3. The boiler requires steam pipes, water pipes, fuel supply, electrical connections and can be made ready almost immediately.
Energy-saving renovation Technology of Coal-fired Boiler the operating parameters of blower and induced fan are directly related to the thermal efficiency and energy consumption of coal-fired boiler components. The coal-fired boiler can be reformed with appropriate speed regulating technology, and the drum can be adjusted according to the load of the boiler during the transformation. It can not only save coal-fired boiler, but also save the power consumption of fan, so that the energy-saving effect can be achieved.