Advancing the ignition point of coal, the temperature of the furnace to improve the ash carbon content decreased. Smoke swirling mix and strengthen the separation of coke particles in the flue gas, so that it falls on the fire bed and the new layer further fuel burn. Flue gas also strong swirl in the flue gas CO, H2, CH4 and other combustible combustion gases, thereby improving the thermal efficiency of the boiler is more than 4%. But also improve the boiler output to meet the needs of the production of steam, reducing environmental pollution, expanding the scope to adapt varieties of coal. 2. The air supply and reasonable regulation. In Grate, vibration stove, oven and forth, depending on the characteristics of the combustion process, reasonable air, to promote combustion furnace is very important. As the chain furnace, with grate the fuel is kept in motion, occur sequentially ignition, combustion, burn various stages. Along the longitudinal direction of the combustion grate stages, the partition, the amount of air required in the grate longitudinal direction is different. In the preheating zone of the head and the tail of burnout grate stage, small air requirement in the middle stage of combustion grate, the air amount required.
After the gas hot water boiler hot water boiler vaporization emergency 1. Vaporization handler circulating pump stops abnormally pump failure caused by: ① blower stops running immediately. ② immediately open the door, take measures to pressure the fire, lift the chute gate, cutting off the supply of coal grate. ③ In the case of boiler pressure not greater than 0.6MPa (600KPa), the exhaust valve to follow, only a sharp rise in pressure in the boiler deflated, used only relief exceeds 0.9MPa, and the exhaust process to be carried out slowly, prevention boiler due to loss of pressure and more violently again vaporized. ④ close the boiler water, water main gas valve. ⑤ open stop valve recirculation line, to ensure that the water supply pipe velocity convection heating surface (economizer) to prevent re-vaporization of the economizer. ⑥ The operation of the above operation, at the same time to pay the boiler to reduce the boiler water temperature and the furnace pressure. ⑦ After the boiler pressure is normal, i.e., opening the standby circulating pump, into the normal combustion. 2. Treatment failure or sudden loss of power boiler vaporization of power: ① immediately open the door, lift the coal chute slide gate to take pressure fire measures to reduce the oven temperature. ② Grate with the fastest speed in order in the shortest time to fire onto the slag tap. ③ the degree of treatment in the first case. Once a short time can not supply heating network system, antifreeze should take emergency measures. 3. Due to excessive heat boiler boiler vaporization process: ① the immediate closure of the drum, induced draft fan. ② immediately open the door, take measures to pressure the fire, lift the supply of coal chute slide gate, off of coal, while the grate into fast gear. ③ In the case confirmed the presence of water, the boiler can supply water to the boiler body, boiler out of the water while closing the main valve. ④ Open line stop valve recirculation pump to ensure water velocity convection heating surface of the pipe, to prevent the economizer again vaporized. ⑤ Open circulating pump with jog mode, jog each time less than 30 seconds, again less than one minute jog interval. Jog purpose is to reduce the boiler water temperature, while preventing a large amount of steam into the pipeline system. ⑥ back into place after the safety valve, circulating pump running, and then the normal burning stove. 4. Water boiler system run vaporization process due to water loss, loss of pressure caused by: ① immediately closed drum, induced draft fan. ② out of the water while closing the main valve and the boiler circulating pump. ③ take the same measures to cool the furnace tube described above. ④ Open stop valve recirculation line. ⑤ rely exhaust valve until the safety valve back into place. ⑥ until the boiler water temperature drops below 50 ℃, when the temperature of the furnace temperature less number 200 ℃, again within the boiler feed water, water course to be carried out slowly, to prevent harm to the boiler when the temperature is too large. ⑦ After processing leakage fault, the system time to the replenishment, and out of the water boiler always open the valve, and the circulating pump, and then normal combustion.
Details of operation of the boiler details chemical energy chemical energy Note 1 Note that operation of the boiler, fuel delivery is controlled with respect to the thickness of the layer of coal-fired boilers, the actual operation, the particles of different sizes on the same coal seam, unreasonable distribution, uneven ventilation, combustion is not uniform. The method can be employed uniformly stratified combustion to coal, to improve seam incomplete combustion: first administration of large particles of coal in the lower layer, the upper layer after administration minimal, large particle surface area of small particles of coal, the need to burn a long time, this time is in the air the highest concentration of oxygen lower position; the other hand, small particles of coal on top, large surface area, a low oxygen concentration, full use of excess air. 2, the flow regulating damper excess air ratio is too large, a large loss of smoke; excess air ratio is too small, incomplete combustion loss is large, and therefore need to properly regulate the air flow to minimize loss of two or more. Usually in the flue gas analyzer backpass smoke, the control amount of wind of carbon monoxide is reduced to a reasonable value. For unconditional for gas analysis, empirical judgment by the naked eye can see the flame in the furnace, the flame pale described excess air amount; brown opaque flame, smoke black smoke indicates incomplete combustion. 3, there is a 1mm thick scale surface water quality management experiment boiler heating surface, waste of fuel from about 3% to 5%, in the presence of 3mm thick scale, waste of fuel of about 5% to 10% . Water two general steps: pre-treatment, ion exchange or reverse osmosis. 4, cleaning blowdown gray scale or fouling deposition in the heating surface, increased heat resistance, reduced heat absorption wall, to improve the furnace exit gas temperature, boiler output decreased, but to increase the amount of cast coal, causing furnace exit gas temperature further improve a vicious circle. Therefore, timely cleaning clear dirt is particularly important. 5, the energy efficiency of the heat insulation testing industrial importance boiler showed small boiler in the case of good thermal heat radiation loss is about 3%, if the wrong selection insulation material, the thickness is too small, or even damage, does not include local heat, heat losses will be higher, the boiler has been running, has been caused by waste heat into the air. When the shutdown check whether the furnace wall insulation bricks off; isolated brick flue check is complete, to avoid shorting the flue gas; outer portion boiler, steam pipes and other insulation damage to be repaired; when heat insulation, low thermal conductivity of the material ( i.e., materials with good thermal insulating properties) on the inner layer having a better thermal insulation effect; respond to the economizer outer insulating layer for laying under conditions permitting. 6, to solve the problem of air leakage air leakage boiler boiler unit during operation is a common problem, the need to ensure the tightness of the boiler, furnace air leakage above all, do not close the site to check the furnace wall, door, inspection holes, etc., can be candles law, candles near these places, to observe whether the candle flame inward deflection to judge. Second leakage tail heating surface, the flue stack leakage mostly welding cracks, elbow bend, the expansion joints wear wear; mostly air superheater corrosion or wear leading to leakage through the pipe, the boiler shutdown should focus an examination.
After the boiler put into use, such as the hotel responsible person to give us feedback: fast boiler advanced product design, simple and intuitive operation, the most critical is energy saving, low NOx emissions, can be used in the Beijing area. Compared with other boiler brands, fast Boiler made us worry. --customer feedback