Why horizontal gas steam factory used steam coal boiler agent wood boiler agent to run under negative pressure? Horizontal Gas-fired steam boilers are generally negative pressure operation, if the pressure is running high temperature flue gas will cause the furnace to burn jet furnace walls and insulation, but also endanger the safety of operating personnel , the negative pressure is not too large, generally -10 ~ -30Pa, small oil-fired boiler is generally because there is no draft fan for the combustion positive pressure. For improving the thermal efficiency of the boiler has the following methods: a low pressure industrial boiler manufacturers has been designed in consideration of the problem of overheating efficiency, device, or change from the flue gas energy aspects is not possible and thus the best energy boiler operation starting from the (here not On the recovered water of vapor condensation). According to statistics survey, the current design of the thermal efficiency of domestic low-voltage industrial boilers is generally 70 to 90%, generally the actual operation of the thermal efficiency of about 60 to 80%, some even below 50%, a small low pressure industrial boilers as long as the operation, maintenance properly, design can achieve the thermal efficiency of the boiler manufacturers. I think the management and operation of the boiler should pay attention to the following points: First, to monitor the boiler exhaust gas temperature. Usually the largest boiler flue gas heat loss is a loss, so control the boiler flue gas temperature is very important, general industrial boilers low pressure gas (mainly refers to less than 10 tons of boiler and pressure of 1.6MPa, the same below) of the exhaust gas temperature is 150 ~ 180 ℃, oil-fired boiler exhaust gas temperature is 210 ~ 240 ℃, when the exhaust gas temperature is too high to find the cause and timely elimination. Causes of high temperature exhaust gas boiler are: a chamber negative pressure is too high, short-circuiting flue gases, the heat pipe 3 soot is too thick, too thick scale pan 4, etc., oil-fired boiler exhaust gas temperature is too high reasons : 1 air not adjusted oil, the oil is not completely burned in the chimney secondary combustion occurs aft, 2 soot too, the need for timely cleaning, the flue gas short circuit 3, 4 is too thick scale, etc. second, the control of boiler blowdown rate. General industrial boiler blowdown rate controlled at 5 to 10%, in the pot of water to ensure that qualified (mainly total alkalinity and pH) under the premise of boiler blowdown rate as low as possible, the sewage to adhere to the "ground row, row less, uniform discharge "principle. Third, the maintenance of good boiler furnace wall insulation. Boiler heat loss is also a relatively large heat losses, now the boiler manufacturers in the manufacturing and design has been well thought out, so we do not need to change, we just trying to be difficult to maintain. Outsourcing surface temperature generally does not exceed the boiler 50 ℃, such as too high will have to find out the reasons, timely elimination. Boiler insulation should always be kept dry for gas boilers, pressure must not run long, or easy to damage the coal furnace wall and gate and so on. Fourth, adjust the ratio of fuel and air volume, complete combustion of the fuel as possible. Small boilers generally do not have the amount of wind testing instruments, we can only go by experience adjustment. For oil-fired boiler, the normal combustion flame was yellow-white, non-glare, flame stability, no visible smoke chimney; for gas boiler, the normal combustion flame as a light yellow, no visible smoke stack, substantially cinder burn coal particles as uniform as possible. Fifth, there must be complete boiler water treatment. Complete boiler water treatment and water quality testing can maximize prevent boiler scaling and correct guidance of the sewage, but it did not do a lot of small boilers, companies usually do not pay attention.
After use throughout the winter, the Central Conservatory of Music give us feedback, six V6-99 fully meet the heating needs of the school. And factory used steam coal boiler agent wood boiler agent fuel and water requirements are not high, urban water and low-pressure natural gas combustion can operate. The most important point is that nitrogen oxide emissions are very low and very happy to recommend it to others to do the brother of boiler units. --customer feedback
Small electric steam factory used steam coal boiler agent wood boiler agents What are the benefits, features? First, electric and coal, oil steam generating comparative advantages and disadvantages: advantages and disadvantages of coal: Advantages: coal is the most economical energy per kilogram of coal can produce more than 5,000 calories, can produce about 6 kg steam (theoretical value). Both economical than electric, fuel oil and natural gas. Disadvantages: 1, low efficiency, although theoretically per kilogram of coal can produce more than 5,000 calories, but due to the limitations of coal-fired boilers and human factors affected the Boilermakers, the real heat of the steam is converted to produce much smaller than the theoretical value, the heat utilization rate of around 60%. 2, can not do automatic control, if the device is not continuous steady steam steam that instant steam consumption fluctuations, the steam produced by the boiler with the steam in the bottom of the valley steam equipment can only let go waste. 3, need specialized operators, high labor costs. 4, do not meet the requirements of modern environmental protection, to ban small coal-fired boilers is the trend. The advantages and disadvantages of fuel: fuel meets the requirements of environmental protection, the state has not been expressly provided, however, based on current oil prices, its economy has ceased to exist. Per liter of oil can produce more than 18,000 calories, about 60% utilization, we can produce about 10 kg of steam. Which produce one ton of steam costs around 800 dollars (at current prices). The advantages and disadvantages of heating: Cons: Because electricity is converted from the other sources of energy, so the relatively high price point, once electricity can produce about 1.5 kg of steam. Calculated to produce 1 ton of steam costs about 400 yuan or so based on the current average domestic electricity bill. More expensive than coal.
SZL series coal fired steam factory used steam coal boiler agent wood boiler agent, working capacity is from 6 to 30 ton. Our client need a set of 10 ton steam boiler for his paper factory, which is available for biomass fuels like wood pellet, rice husk, etc. According to design, those coal fuels will be sent to boiler chamber by chain grate, transferring coal fuels to thermal power. Although chain grate boiler has lower thermal efficiency than circulating fluided bed boiler, but considering boiler system price and its fuel costs, to 10 ton steam boiler, choosing SZL series chain grate boiler is more economical in total. Besides, our SZL series boiler, has automatic operation system, safe and convenient to boiler operator. Indonesia has rice, cheap and high quality coal resource. Our clients in local prefer coal fired boiler than other boiler with different fuels.