Fuel oil-fired industrial distributor 4t boiler azerbaijan boiler water filling operation process in preparation for the next cold case into operation, we must first understand the boiler water filling system without fault, and therefore should be done before firing boiler water filling trials to test boiler water filling system is normal, pipeline The valve leaks. Operating Procedure: (1) upon inspection of boiler meet the operational requirements, in order to carry out work in Sheung Shui boilers; before (2) Sheung Shui, you must get in touch with the boiler water quality testing staff to ensure that water treatment is working properly, to avoid affecting the boiler water filling; (3) open the power, boiler exhaust valve opening, to start the pump, check the boiler water pressure greater than the working pressure, to open the valve, to boiler Feed; (4) fuel boiler Feed simultaneously, open the drain valve drainage , the inner opening the drain valve, the drain valve opened outward, outer closed drain valve, the drain valve closed inner, outer 2nd opening the drain valve, 2nd outer drain valve closed, after rinsing pot, close the drain valve to continue on to the boiler water; (5) the pot water level reaches the normal level, to turn off the water supply pump is stopped, the exhaust valves; (6) for water drainage test table, the drain valve open water table, the water table confirm normal, closed drainage water table valve, waiting for ignition. Sheung Shui operational matters should be noted: Sheung Shui to oil-fired boiler water level should not exceed the normal water level, because when the boiler ignition, the boiler thermal expansion of water, the water level rise would exceed the maximum safe water level. If this happens, the water level should be adjusted by sewage.
2. Which country will the boiler be used in?
Gas oil fired water tube boiler working principle
Cade Shopping Mall is located in central Shanghai Hongkou District, Shanghai Daily larger flow of people in the region. The introduction of Shanghai air pollutant emission standards, industrial distributor 4t boiler azerbaijan flue gas emissions of nitrogen oxide emissions to less than 80 mg / m, Shopping Mall a coal-fired boilers have been used for many years, NOx emissions far super to this request, the urgent need to replace more environmentally friendly low nitrogen emission boilers. Other units through the use of fast Boiler introduction and understanding, determined and fast boiler to achieve cooperation, party fast to their specific needs to recommend one condensing gas hot water boiler of a 4.2MW for heating needs of the shopping center.