In the boiler of natural circulation, water pressure-fed by the feed pump, the economizer heat into the evaporation system, the downcomer in the furnace outside, not heated, the working fluid flowing in the pipe water; in the heated evaporation pipe, the flow of the inner tube soda compound. Since the vapor density less than the density of water, so that the water drops of the inner tube greater density than soda mixture in evaporator tubes. Under the effect of the difference in density, the lower header on both sides of the working fluid pressure imbalance exists, so as to promote the flow of the working fluid circulating in a closed system evaporation.
Around the city to promote the coal to gas project, the major institutions of the heating system put forward higher requirements. Central Conservatory of Music is available to students and teachers clean, safe, comfortable, energy-efficient heating environment, protect the health of teachers and students, to transform the traditional any recruit for 2nd class boiler attender in nagaon paper mill un assam treatment. Praise fast boiler Willie sharp series obtained in the transformation of low nitrogen boiler major institutions in Beijing, the Central Conservatory of Music in late 2017 with the signing of fast boiler boiler purchase contract, ordered six Willy sharp series V6-99, to for the entire school's heating facilities.
A low nitrogen stainless steel tubing is often used as a boiler flue gas duct, in order to energy saving, the use of very low thermal conductivity advanced super slim centrifuged as glass wool insulation material in the outer tube, it is possible to sufficiently reduce the heat radiation loss of a boiler, but also very beautiful practical.
How full any recruit for 2nd class boiler attender in nagaon paper mill un assam water treatment? 1, the boiler is full of water refers to: (1) the water level is not visible or not, a high level alarm; (2) steam temperature decreases, main steam isolation valves and the turbine inlet valves visible white steam; (3) turbine or steam pipe occurs water hammer; (4) water flow is not larger than the normal steam flow. 2, causes: (1) water supply is automatically jump manually, resulting in abnormal increase of water supply; (2) safety valve on the drum or steam header, resulting in up water or with water; 3) evaporation boiler more overload occurred priming. 3, processing method: a boiler steam pressure and when a normal pressure, the drum water level rises, exceeds + 50mm, the following measures should be taken: (1) the flushing drum were compared with two level table to check instructions are correct. (2) from the automatic to manual adjustment of water supply, water supply and close the door manually turned down and to reduce the total water supply amount adjusting gate. If after treatment b above, within the drum water level is still rising, exceeds + 75mm, should be carried out the following measures: (1) to open the door for emergency drain drum should be put to the normal water level water level shut down immediately. (2) The steam temperature, the heated reducing or closing off the small door, door open and main steam superheater tubes hydrophobic hydrophobic gate. When the treated drum water level continues to rise, and exceeded the upper drum water level meter water level visible, on emergency shutdown, as soon as possible with the main pipe splitting, immediately stop the water, recycled to open doors, turn on the water to strengthen the boiler and steam drum note an upper level of the water table appears to be put to the normal water level off. Standby furnace often the case, the value of the long obtaining consent, according to Stoke furnace operation. C If the drum can not see when the water level within the water table, not in time, should take the following measures: (1) were compared with two wash drum water level table, check the instructions are correct. Full drum water level tables turn on the water door, turn on the water and then slowly close its doors, as there is water in the water table appears, and water levels continue to rise full of tables full of water and has not been proven boiler water level gauge steam over the side of the tube, press the emergency shutdown process. (2) open the door turn on the water table level, and slow to close its doors after the turn on the water, the water level in the water table invisible. To prove a serious full of water, soda and then close the door, turn on the water to open the door, the water level of the water table memory after the release to do, turn on the water shut the door immediately. Ajar quickly and valve inner water table level occurs, and filled with water, before this time has exceeded the determination level of the steam drum level side through the tube sheet, emergency shutdown should be treated as soon as possible and the manifold splitting. (3) When the water level in the boiler accident occurs, it is difficult to judge if the water level should be shutdown immediately. After the shutdown called by the water method called water, check the water level in the drum.