Trap in the application, which varies the operating conditions, the displacement in the choice trap The heating system should be several times larger condensed water discharge than normal computing, and be chosen according to the diameter size. Evaporation of less than 4 tons of steam hot selling boiler 1ts, water regulator should be installed automatically, and manual means provided with feed water controls stoker operating site.
Foshan Gaoming Liu Ling Textile Dyeing and Finishing Co., Ltd. was founded in 2007, enterprises comprehensive strength, advanced processing equipment, detection means perfect, has a complete quality assurance system, the introduction into a large number of advanced production equipment, to ensure that technical standards and products stable to improve the quality of laid a solid foundation, enjoy a high reputation in the industry. Liu Ling Gao textile company twice with my company were to buy a 20 tons of steam and a whole 10 tons of steam condensing steam hot selling boiler 1t fuel gas for the production of textile dyeing and finishing company. Fang fast with strong comprehensive strength and improve the service system to win the favor of the other side, communication from the initial to the final boiler factory-installed square fast all uphold the customer's perspective to think and observe the service concept, for the sake of clever Liu Ling textile companies according to the company's actual demand for textiles, the development of specific programs.
When the condensing boiler is used, it adopts a special principle to make use of the way of water circulation to produce a certain heat exchange so as to achieve the desired purpose. Although the price of the integrated condensing boiler will not be too high, and the operation is very simple, and has good safety performance and so on, but in the process of operation, it is necessary to pay attention to the following points.
1, pre-service preparations for long-term non-operational or brand-new fully premixed condensing boilers, clean up the system with water before starting again, this is an extremely important preparatory work for condensing boilers. The operation of the docking will be of great help. And condensing boiler manufacturers remind you to start in the correct order, such as turning the circulating pump on before you can ignite it.
2, in order to control the details of the operation of the condensing boiler during its operation, in order to make it work better, the pressure in the boiler should always be in a stable state, and the temperature in the boiler should be controlled. Therefore, at any time to monitor and monitor the discovery of any changes should be made certain adjustments. And condensing boiler manufacturers emphasize that the gas in the pipe network should be discharged from time to time, which can prevent vaporization well, at the same time, it should be carried out regularly and the quantity of water in the pipe network should be reasonably distributed.
3, to control the pressure in the boiler well, if the pressure inside the boiler suddenly rises very high during the use of the fully premixed aluminum condensing boiler, it should be immediately found out the cause, usually because the water temperature is too high for gasification. Therefore, the water temperature should be properly lowered to solve this problem. It is also possible that clogging occurs because the dirt in it has not been cleaned up, so the cleanup should be done in a timely manner. If, however, the pressure of the condensing boiler is suddenly reduced, the boiler should be rehydrated in a timely manner, as this is mainly due to the shortage of water.
Factors affecting thermal efficiency of hot selling boiler 1tIn order to improve the boiler thermal efficiency, save fuel, and increase the thermal economy of boiler work, it is necessary to analyze the factors that affect the boiler thermal efficiency. According to the formula of counter-equilibrium efficiency, the factors affecting thermal efficiency are heat loss of exhaust smoke, heat loss of chemical incomplete combustion, heat loss of mechanical incomplete combustion, heat loss of heat dissipation and physical heat loss of ash. These heat losses are analysed below.