For a long time, the industrial boiler heaters and burner are attributed to two different sectors each R & D re-combination, but the overall performance of the gas boiler, there is a qualitative impact. Fang fast R & D team after two years, estimates adjusted 300 times, breaking the status quo burner and boiler production separate, optimized depth coupled combustion system and heat transfer system architecture, combined boiler and combustion system, combustion system and successfully developed the depth of the heat transfer system coupled "Euromonitor θ5", so that gas-fired boiler into a complete energy system, to achieve a qualitative leap. "Euromonitor θ5" additional air pre-heater, cold air through the heat exchange tubes and the body opening for the flue gas countercurrent heat exchanger, the exhaust gas temperature is lowered while saving fuel; using a condenser, economizer flue gas heat recovery, thermal efficiency of the boiler can be increased by 10%; the use of FGR flue Gas recycling technology and Ultraten wing technology, improve heat transfer efficiency, emissions of nitrogen oxides emissions standards in line with domestic cities.
Hot water industrial boiler heaters should be cleaned regularly with hot water boiler overhaul to the timing of its finishing and maintenance, eliminating potential threat, but also the timing of its identification and testing. Check electric boiler inside there is no scaling or corrosion, while viewing their welding there is no gap or crack, do not underestimate that little slit, attack the source of some dangerous trouble is precisely that. Take a look inside the tube there is no wear and corrosion, especially at the interface wall. View pipes have not presented twists and turns, drum kits, depression, overheating and so on. Metal temperature on the electric boiler equipment also want to see, once overheated cooling is necessary to adopt appropriate treatment. Check whether the automatic control systems and related instrumentation also robust and flexible to use.
ZG Boiler has been closely involved in boiler since its inception in 1945. It was formerly know as ZG Boiler. ZG Boiler also supply to industrial boiler export to regional countries like Middle East, Japan, China, Malaysia, Indonesia, India, Thailand, Singapore, Australia etc. In 2014, ZG boiler company in Malaysia have cooperated with six company with seafood factory, paper mill, Palm Oil Mill, PVC mfg, Plywood. Boiler price in Malaysia, please contact our online service.
Nowadays, the use of gas-fired steam boiler has become more and more frequent, and the boilers all over the country have changed the use of gas-fired boiler with each passing day. Although the domestic professional gas-fired steam boiler is stable in operation and less energy-saving and consumption-reducing in sewage discharge, it is necessary to use proper maintenance in the case of long-term non-use in order to carry out normal use. Specific gas-fired steam boiler maintenance methods in the case of not in use and see below for detailed analysis of the following:
1: dry maintenance of gas-fired steam boilers should remove the boiler water after shutdown, and then thoroughly remove and rinse the dirt from the interior. And keep the oven dry so as not to be seduced. You can dry the chamber with a light fire, but not with a fire. Also be careful to close all hand-hole piping valves and place the quicklime tray in the drum. Check the boiler at least three months without using a gas-fired steam boiler for a long time. If the quicklime in the chamber is crushed into powder, the new lime needs to be replaced immediately to ensure that the drying protection in the furnace of the gas steam cooker is not corroded by moisture.
2: in addition to dry maintenance, wet maintenance of gas-fired steam boilers can also be done by means of wet maintenance, which is to remove internal dirt after discharging the water in the furnace, and to fill the chamber with treated water and then heat it to the required temperature. The gas in the water is then discharged out of the furnace and all valves are closed. In this way, the furnace is filled with water to complete maintenance. Of course, wet maintenance should not be used in cold weather to prevent water icing and damage to the tank. It can be seen that the gas-fired steam boiler in the case of not in use is mainly dry and wet method of maintenance, which kind of specific use Maintenance method according to different site and climate conditions to make flexible choice.