Still 8 cultural and creative industrial park is located in the Chaoyang District, Beijing, Bali Zhuang Chen Lin, No. 2, construction area of 493,300 square meters. Surrounded by quintessence of Court, Red Sandalwood Museum, Shanxi Museum and other famous attractions. Due to its special geographical location, has very stringent requirements for providing heat boiler plants. Carefully selected to finalize cooperation with our company, signed a two He Lide series complete condensation pressure hot water boiler.
These are just three points Henan fast boiler gas boiler you organize the selection criteria, in fact, if you want to choose a real business needs for gas-fired boilers, but also from many aspects insight into the boiler, such as: the use of advanced technology gas boilers, operating efficiency, footprint, Applications, ease of operation, security systems and so on.
Boiler outdoor detection means mounted matter detection device can acquire the outdoor temperature of the outdoor will transmit a signal to the control room boiler, the boiler operator may then adjust the output power of the boiler, to heat buildings better. Detecting means attached to outdoor some caveats, the following is a specific description. Correctly installed outdoor temperature is the basis of the detected control function. The detector must be installed outside the building heating, 1/2 height of the wall, facing north or northwest direction, away from the local flue, doors, windows and direct sunlight. 1, the detector should be mounted on a smooth, flat wall 2, the maximum length between the detector and the control panel are an outdoor 50m3, any user connection cable conduit must be away from the power cord (230v) 4, the detector and the control panel can not have joints between the wires, if unavoidable, these joints must be well outside the probe seal mounting step 1, the detector opens the protection cover, is an adapter plate is rotated counterclockwise and the fixing hole. 2, find a fixed point as a template with a protective case. 3, removed the protective box, punching, use of the expansion plug. 4, two plugs using the supplied protective box fixed to the wall. 5, two wires connected to the connection plate, no need to determine positive and negative. 6, the cable seal tightening nut sleeve, close protection cover. Outdoor temperature controlled heating profile formed water temperature set point for the water temperature to maintain a certain level. Adjust the heating profile in different ways can be used to meet the heat output and room temperature. When the heating curve slope increases, the water temperature as the outdoor temperature decreases. Or, in other words, if the indoor temperature is not displayed correctly when the cold outdoors, is displayed correctly when the outdoor temperature is high, the heating curve slope must be re-adjusted. Increase slope: especially when the outdoor temperature is low when the water temperature increase. Reduce slope: especially when the outdoor temperature is high, reduce the water temperature. Set the heating chamber 20 is a graph of reference, such as the set point changes, it will automatically change the heating curve. Heating curve parallel displacement for changing the average flow temperature of the day, in other words, if the room temperature is too high or low, must be parallel displacement curve. The condensing boiler control automatically the heating curve to apply to the weather conditions, without resetting the heating curve slope, as long as can be on or off. To use this feature, the following points must be observed: 1, must be connected to the indoor sensor 2, 3 indoor setting change must be selected between 1 and 99, with reference to a thermostatic chamber without installing radiator valves, with reference to the sensor chamber is to install an indoor place (the installation of such a valve must be fully opened or closed if the sensor is used indoors, the compensation variable weather compensation function is activated by this parameter.