Tai Chi, Jiaozuo City, Jiaozuo City Sports Center is one of important sports infrastructure, a total area of 11.73 hectares, held several international events. With strict management in Henan Province for air emissions of pollutants, Jiaozuo City, also launched the governance of coal-fired boilers, thermal power and other equipment. Jiaozuo Sports Center actively cooperate with municipal workers, took the lead from coal to gas activities, the serious pollution of the original extent of coal-fired boilers to replace gas boilers. Gas boiler cleaning binding understanding of the market, to achieve cooperation with the finalization fast boiler by providing a fast side 2.8MW integrally condensing gas indonesia coal fired hot water boiler (WNS2.8-1.0 / 95/70-YQ), it is used to Sports Center provides heating and hot water.
Pressure boilers Products of the non-pressure indonesia coal fired hot water boiler, also called pressure boilers, boiler usually refers to the top does not bear the water column static pressure of the heating system. That is quite an open hot water tank. Meaning pressure boiler: boiler body opening to the atmosphere. In any conditions, the boiler at the water line are zero gauge pressure boiler. Pressure boilers Model consists of three parts, connected by a hyphen between the parts. Categories: pressure hot water boiler is mainly classified by fuel can be divided into CLDR (CWDR) often piezoelectric hot water boiler, CLHS-YQ (CWNS-YQ) pressure fuel (gas) hot water boilers, pressure coal-fired hot water boilers. Model: The first part of the model by atmospheric pressure boiler code, pot-type code, combustion equipment code, the rated thermal power four sections. Boiler pressure is represented by C code example: CLSG0.35; 95/70; W12 represents a vertical pipe fixed grate boiler pressure, the rated thermal power of 0.35 mW, rated outlet water temperature was 95 deg.] C, the nominal temperature of the water inlet. 70 ℃, burning anthracite class I, a second design of the boiler. Product Structure: The overall structure of pressure boilers and boiler auxiliary equipment including two parts. Boiler furnace, drum, burner, water wall superheater, economizer, air preheater, and the furnace wall, etc. The main frame member constituting the core part of the steam production, called boiler. Boiler body is in two main parts and drum furnace. Also known as the furnace combustion chamber, fuel combustion for space. The solid fuel on to the grate, referred to as a fire bed combustion furnace Stoker, also known as fire bed furnace; solid fuel furnace liquid, gas or pulverized, is injected into the combustion chamber is called the fire chamber burner, also known as the furnace fire chamber; air coal particles burn hold it was boiling, and the furnace is inferior fuel suitable for combustion is called fluidized bed furnace, also called fluidized bed furnace; coal particles so that an air flow rotated at high speed, and strongly called fire cylindrical cyclone furnace hearth. Furnace design needs to fully consider the characteristics of the fuel used. Each boiler should be fueled with the original design of the fuel. Boilers running economy and reliability are likely to vary greatly reduced when using the characteristics of fuel combustion. And the natural circulation drum is repeatedly forced circulation boiler receiving feedwater to the economizer, the coupling cycle and supplying saturated steam superheater cylindrical vessel. Simplified drum made from high quality steel plate, is one of the heaviest components of the boiler. Safety knowledge; boiler is a high-temperature, high-pressure thermal equipment, is one of special equipment, widely used in government agencies, public companies and all walks of life, are dangerous and special equipment. Event of an accident involving public safety, it will cause huge losses to the state and people's lives and property. For public safety, people's lives and property safety, according to the State Council, "Regulations on Safety Supervision of Special Equipment", the boiler should use full attention the following matters: 1, should be accompanied by safety technical specifications of the factory boiler design documents, product quality certification, safety and the use and maintenance instructions, supervision and inspection certificate (safety supervision, inspection and performance certificate). 2, boiler installation, maintenance, alteration. Engaged in the installation of the boiler, maintenance, renovation of the unit shall obtain special equipment installation and maintenance certificates issued by the Provincial Quality and Technical Supervision, before engaging in the boiler installation, maintenance, alteration. Construction unit before construction will be prepared for installation, maintenance, alteration in writing inform the special equipment safety supervision and management department of the municipality or district, and will start informing sent to the local county level Quality and Technical Supervision for the record, told immediately after construction. 3, inspection of boiler installation, maintenance, transformation. After construction, the construction unit To State Quality and Technical Supervision of Special Equipment Inspection and hydrostatic testing of the boiler installation supervisory inspection declaration. After passing by the State Quality and Technical Supervision, State Special Equipment Inspection, County of Quality and Technical Supervision involved in overall acceptance. 4, registration boiler. After the boiler inspection, the use of units must be in accordance with the "special equipment registration and use of management rules", fill "boiler (census) Registration Form", the State Quality and Technical Supervision to register and obtain a "registration certificate to use special equipment safety . " 5, operation of the boiler. Boiler operation must be performed by trained and qualified to obtain "special equipment operator certificate" certified personnel to operate, must strictly abide by the rules and eight systems, six record. 6, check the boiler. Periodic inspection of boiler once a year, not be used without safety periodic inspection of boilers. Safety accessories safety valve of the boiler regular inspection once a year, pressure gauge biannually verified, may not be used without the periodic inspection of the safety accessories. 7, non-pressure boilers will be installed for the boiler pressure. Do not use water level gauge, safety valve, pressure gauge three safety accessories insufficiency boiler. Daily operation and maintenance: ⒈ chemical contact, turbine attendant prepare enough desalinated water, oxygen, water passing temperature no higher than the drum wall temperature 50 ℃; Sheung during hot water temperature should not be to the drum wall metal temperature difference greater than 40 ℃ .⒉ new installation or after recording before overhaul boiler Feed expansion departments indicated .⒊ Sheung summer time less than 2 hours, at least 4 hours in winter, when the temperature and Sheung drum wall temperature difference of less than 40 ℃ how reheater be preserved? ⒈ turbine after playing brakes, boilers ensure a blower, an induced draft fan is running the best cross reserved two oil gun .⒉ open reheaters to the empty exhaust steam reheater hydrophobic doors and air doors corrosion, anti-corrosion of the reheater steam temperature is lower than a predetermined deg.] C for 400 .⒊ control drum water level within the permissible range .⒋ preservation time less than 20 minutes after stopping two oil gun operation guaranteed .⒌ when the furnace pressure 50--100Pa, each of the flaps open, baffle for ventilation less than 5 minutes, stop sending, fan, each of the flaps closed tailgate may be appropriate to accelerate Sheung speed.
How to provide boiler thermal efficiency thermal efficiency of the steam boiler has the following methods: low-pressure boiler at the factory has been designed considering the problem of thermal efficiency of the boiler, the flue gas from the device or change little aspects of energy-saving possibilities, it is best to start from the energy-saving operation (here talk recovered water vapor condensation method). The current design thermal efficiency of domestic low-pressure boiler is generally 70 to 90%, generally the actual operation of the thermal efficiency of about 60 to 80%, some even below 50%, a small low pressure industry as long as the operation, maintenance properly, can meet the design thermal efficiency of manufacturers. I think the management and operation should pay attention to the following points: First, the boiler flue gas temperature monitoring. Typically the maximum exhaust heat loss is loss, it is important to good control of exhaust gas temperature, exhaust gas temperature is generally low pressure coal-fired boiler of 150 ~ 180 ℃, fuel boiler exhaust gas temperature is 210 ~ 240 ℃, so when the boiler to find out why when the exhaust temperature is too high and promptly eliminated. Coal-fired boiler flue gas temperature is too high reasons are: high furnace pressure; shorting smoke; thick soot on the heat pipe; thick scale pot like. High temperature fuel exhaust reasons are: 1 air not adjusted oil, the oil is not completely burned in the chimney the secondary combustion occurs aft; 2 soot too, the need for timely cleaning; 3 shorting smoke; 4.... thick scale; Second, controlling blowdown rate. Without restricting the general rate of industrial sewage control in 5 to 10%, in the pot of water to ensure that qualified (mainly total alkalinity and pH value), the blowdown rate as low as possible, the sewage to adhere to the "ground row, row less, are ranked "the rules. Third, the maintenance of good furnace wall insulation. The heat loss is also a relatively large heat losses, now the manufacturers in the manufacturing and design has been well thought out, so we do not need to change, we just trying to be difficult to maintain. Outer surface temperature generally does not exceed 50 ℃, it will have to find out the reasons such as too high, and remove. Boiler insulation should always be kept dry, for coal, not a long positive run, or easy to damage the coal furnace wall and gate and so on. Fourth, adjust the ratio of fuel and air volume, complete combustion of the fuel as possible. Generally do not have a small amount of wind testing instruments, we can only go by experience adjustment. For oil, the normal combustion flame was yellow-white, non-glare, flame stability, no visible smoke chimney; For coal, the normal combustion flame pale, no visible smoke chimney, basic cinder burn coal particles as even as possible. Fifth, the need for a sound water treatment. Improve water treatment and water quality testing can maximize prevent fouling and correct guidance of the sewage, but it did not do a lot of small, companies usually do not pay attention.
1.High efficiency: the corner tube hot water boiler grate structure design is reasonable, precision casting, scaly type fire grate assembly clearance is small, little grate coal leakage, replacement without stopping furnace. The wind chamber adopts isobaric wind chamber with small throttle structure, good sealing, air distribution uniformity, and can control the combustion section for air volume, in order to obtain the optimal combustion state; in the front arch region by enhancing the combustion technology, mechanical loss of incomplete combustion rate was only 7%, the authority testing the thermal efficiency up to 82% above, can bring huge economic benefits to the user.
2.Environmental protection: the excess air coefficient type hot water boiler tail heating surface tube after only 1.4~1.6 angle, not only reduces the heat loss of exhaust gas, reduce the fan power consumption, but also greatly reduces the environmental pollution of boiler room.
3.Security: corner tube hot water boiler wall mounted light insulation material, covered with a compound silicate board, then the metal plate reinforcement, no brick structure, excellent insulation effect, at the same time the boiler operation and control of high degree of automation, convenient operation and safety.