Former Lu'an gas steam water tube boiler with superheater installer to install gas steam boiler, be sure to fill out the "boiler installation started this book", incidentally include at least the following material to the boiler management authority customer location gas boiler steam boiler installation license application formalities, construction can be permitted rear work: ① gas steam boiler installation license copy; ② gas steam boiler installation boiler installation started this book and embodiments of the boiler; ③ gas steam boiler certificate material; ④ boiler room equipment boiler room equipment layout plan and design drawings; ⑤ installation companies operations staff to participate in professional certification. Former gas steam boiler installation, be sure to install the company also completed incidentally permitted "to install the boiler started this book" to the gas steam boiler and pressure vessel inspection quality inspection authorities at the customer site signing "the agreement to install quality of responsibility" by the Inspection Department of the gas-steam standard for the installation of the boiler to monitor.
In order to promote technological progress and sustainable development, improve environmental quality and protect public health, recently, the Liaoning Provincial People's Government of air pollutants for coal-fired power plants developed specific criteria (hereinafter referred to as the "standard"). This is the first time a set of policies Liaoning Province for air pollutant coal power plant.
"Standard" provides for pollutant discharge limits, surveillance and monitoring requirements within the jurisdiction of coal-fired power plant in Liaoning Province atmospheric and fugitive emissions control requirements. Since the implementation of the standards, air pollutant emissions coal-fired power plants all within the jurisdiction of Liaoning Province will be executed in accordance with the provisions of this standard.
2, since January 1, 2019, the emission limits of existing single output and more than 300MW generating units supporting the provision of a coal-fired power generation boilers execution table.
3, since 1 December 2020, the emission limits of existing single output 300MW generating units supporting the coal-fired power generation boilers and other power boilers as specified in Table 1 execution.
Sampling the exhaust gas (1) power plant, to be carried out in a predetermined position in accordance with the type of monitor emissions monitoring contaminants. In the discharge of pollutants should be set up to monitor the position of long-term monitoring holes, sampling platform and related facilities. When the sampling platform height from the ground greater than 40m, should be set by a lift platforms, lifts or other convenient and safe facilities. No elevator or elevator building coal-fired power plants, when the sampling platform height from the ground greater than 20m, should be set up safe, convenient electric monitoring equipment hoisting facilities.
Composition structure (3) continuous monitoring system atmospheric pollutants, technical requirements, test items, test methods and installation, commissioning, acceptance, operation management, data processing, etc. according to the provisions of HJ75 and HJ76.
(5) continuous monitoring system meter of air pollutants detection sensitivity, detection limit, and should meet the range of low concentrations of pollutant emission monitoring technical requirements, the concentration of nitrogen oxides include nitric oxide (NO) and nitrogen dioxide (of NO2), Determination of nitric oxide only has the ability to configure the analytical device of nitrogen oxides NO2 / NO converter.
(7) for coal-fired power boiler emissions of air pollutants sampling monitoring, sampling frequency, the sampling time and the operating load requirements,, HJ / T397 and related predetermined low exhaust gas concentration monitoring is performed according to specifications GB / T16157.
(9) shall be in accordance with the provisions of the enterprise "Environmental Monitoring and Management Measures" and the HJ819, HJ820 requirements of pollutant emissions and its impact on environmental quality around to conduct their own surveillance, monitoring and save the original records, public information.
Determination of air pollutants fired power plant analysis are shown in Table 2. After the release of the present embodiment national standard method of monitoring criteria pollutants, such as applicability to meet the requirements, the same applies to the determination of the corresponding standard contaminants present.
2, responsible for overseeing the management of this standard by the executive authorities and the standardization of administrative departments above the county level environmental protection. The results of the environmental protection departments at all levels and other relevant units in the enterprise supervision and checks can be instantly sampled or monitored the scene as determining whether acts of sewage meet emissions standards based on the relevant environmental protection and the implementation of management measures.
Steam water tube boiler with superheaters should pay attention to safety: Currently people to choose when buying a steam boiler, require people noticed aspect is the issue of security which, after all, now people go to see when people can well see from the selective portions inside to see a completely different part, this is a different situation is now well out of the analysis, in fact, this is not the same part of the terms of, and in accordance with safety aspects are now people see when better to see, and this is a way for people to better see inside the selective section not the same part.
After saving gas water tube boiler with superheater also need to test it? In general, the boiler before being put into normal use, will be through the test to ensure normal operations of the respective other auxiliary elements; while ensuring smooth and safe operation of the overall state of the boiler. So, with the increasingly stringent national environmental policy, the transformation of the boiler has been steadily advancing over the country, it is also part of the boiler users, in order to save the drawing efficiency or other reasons, no longer boiler test, then, after what energy-saving gas-fired boiler also need to test it? in general terms whether it is a new boiler or after the transformation of the boiler before being put into regular use are required to test, and to do at least two advantages, boiler components and raw after the transformation necessary to ensure can be configured between organic combination boiler, ensure the transformation of boiler operating efficiency, stability, safety has improved. The second is to ensure timely corrective action process is in the process of debugging abnormal phenomenon, to avoid re-enter after normal use, causing unnecessary boiler accident. In short, after the energy-saving gas boiler, put on trial before use or necessary, must not for the easy way or the other reasons cause unnecessary trouble, not worth the candle.