Still 8 cultural and creative industrial park is located in the Chaoyang District, Beijing, Bali Zhuang Chen Lin, No. 2, construction area of 493,300 square meters. Surrounded by quintessence of Court, Red Sandalwood Museum, Shanxi Museum and other famous attractions. Due to its special geographical location, has very stringent requirements for providing heat west heat recovery boiler imaige plants. Carefully selected to finalize cooperation with our company, signed a two He Lide series complete condensation pressure hot water boiler.
The daily operation of the west heat recovery boiler imaige adjustment (regulation Part 2): In a large boiler operating parameters change in the magnitude of the situation, should be used "quick adjustment" and "over-regulation" approach, the parameters can change its trend as soon as possible, the "coarse . " Especially when handling accident, to adjust the water level, particular attention should be. Case of an accident, such as "load shedding" "boiler fire" and the like, when the level variation is very large, and because the "false impact level," the rate of change quickly, operators requires rapid response and regulating. And if the mother controls the water supply system, several furnace influence each other, plus the usual low water pressure, in case of an accident, several furnaces at the same time the water level changes, "over water" is serious, and therefore more in the "coarse" They should coordinate with each other to pass on. Avoid artificially adjusting improper expansion of the accident. E.g. "turbine load rejection" and the boiler because the water level regulating improper fire; for level adjustment improper full of water when the "boiler fire"; even when a boiler blower trip underlayer powder machine speed caused by too much air duct blockage and the like.
Method desiccant in the west heat recovery boiler imaige is deactivated, when the temperature of the boiler water is reduced to 100 ~ 120 ℃, to let go all the water in the boiler, using residual heat in the furnace, the dried metal surface, and to remove the water in the boiler system scale and water residue inside. Then placed in the boiler desiccant, holding the metal surface and dried, to prevent corrosion.
Rated evaporation, refers west heat recovery boiler imaige fuel species design, and operation at the design parameters, i.e. at a predetermined quality of steam (pressure, temperature) and a certain thermal efficiency, long-term continuous operation, the amount of steam produced per hour . The new boiler at the factory, the amount of evaporation on the nameplate marked, refers to the rated boiler evaporation of this.
5, pressure: uniform vertical force acting on the object surface, called the pressure, in units of "Newton (N)", is represented by the last kgf (kgf). 1 kg = 9.81 Newtons force. Vertical uniformly acting on the pressure per unit area of the object, called the pressure, in units of megapascals (MPa). On the habits, often referred to as the pressure of the pressure, so the pressure mentioned in this book, in fact, should be pressure.