1. oil and gas steam the fuel is coal oil and fired boiler in algeria system
A complete gas boiler system mainly includes the boiler body, burner, control system and other auxiliary structures
The fact that we determined to achieve cooperation with the fast the fuel is coal oil and fired boiler in algeria is a very wise decision, after a period of time put into the boiler efficiency significantly much higher than our original boiler efficiency, significantly reduce fuel costs, the economic benefits brought by the boiler is obvious. --customer feedback
20 tph WNS gas-fired steam the fuel is coal oil and fired boiler in algeria for milk products plantThe production and processing of dairy products require a large amount of steam to distill, disinfect, dry, and shape the food. The customer's boiler house is arranged in a single layer. After our technical staff visits the site and communicates with customers, ZOZEN decided to use two units of 10 tph oil and gas dual-use steam boilers in this project. This type of boiler adopts a mechanical and electrical integration structure, generous appearance, less investment in infrastructure; our boiler is strictly in accordance with the requirements of the customer to complete the standard, and we provide full equipment debugging, technical guidance, regular return visits, collection Feedback, which makes customer relieved and satisfied.
The coal fired boiler can be divided into two kinds：vertical boiler and horizontal boiler. And the horizontal boiler is very economic because of its long flue gas flow, slow smoke discharge, high heating efficiency. So it is widely sued in the market. After buying a boiler, it is necessary for them to build a boiler room,in the installation the height of the chimney also need to pay attention. According to the ZG engineer, the chimney height should be accordance with the lowest height of GB13271-2001 stipulation. Only one chimney is allowed in a boiler room. The specific requirements was listed below:
1.When the boiler’s output capacity is more than 1t/h or 0.7MW, a permanent thief hatch and relevant facilities should be setted in compliance with the stipulations of measuring method for smoke and dust of boiler emission, and The determination of particulates and sampling methods of gaseous pollutants emitted from exhaust gas of stationary source.
2. The exit diameter of the chimney should be not lower than the largest load. The smoke flow should not be too fast. when the load of the coal fired boiler is at its lowest level, the velocity of the chimney exit should not lower than 2.5~3m/s.
3. If the chimney heat does not reach the height of the above stipulations, the maximum discharge concentration of the dust,sulfur dioxide, nitric dioxide should be carried out at 50% of the corresponding area and time emissions standard .