Comfortable life of people is inseparable from the northern winter heating boiler, normal, stable heat source is vital to people's lives. But the attendant is an increasingly serious environmental pollution problems, the implementation of coal to gas policy without delay, using the gas hot water boiler seller is the general trend. In order to achieve green heating, the National Tourism Administration Service Center decided to phase out the existing coal-fired boilers, the introduction of clean and environmentally friendly gas hot water boiler. Fast boiler with their own strong comprehensive strength and rich experience in the heating industry cooperation gained the trust of the National Tourism Administration Service Center, and ultimately provide a vacuum hot water boiler (T6-2800 2 sets of 2.8MW by fast Boiler ).
How to choose the right boiler steam solenoid valve tips? Solenoid valve is used to control automation infrastructure element the direction of flow, is actuator; commonly used in industrial machinery and control valves used to control the direction of the medium, so as to achieve the vapor solenoid valve control solenoid valve switch operating principle of the currently used usually over two steam: 1, steam boilers - saturated steam temperature and pressure is relatively stable at temperatures below 250 deg.] C, lower than the working pressure 1.6Mp. It can be widely used in textile, printing, chemicals, plastics, rubber, pharmaceutical, food, building materials, machinery, electronics, surface treatment and research departments as well as bathrooms, dining room, air conditioning and other automatic control system. 2, out of the steam power plant - superheated steam temperature high base pressure changes, temperature up to 400 or more, lower than the working pressure 4.0Mpa. Typically use seal steam solenoid valve broader generic media can be used separately in water, light oil, heavy oil, non-corrosive fluid such as gas and steam. The exhaust system of plant extraction duct draining system and an evaporator, the main medium in the pipeline and a remote two-position automatic adjustment control.
Work and family considerations boiler shutdown boiler inspection carried out maintenance before restarting operation, the need for a series of maintenance work, combined with the user experience and learning references, be aware of the following specific boiler maintenance work and family considerations. 1. Preparation (1) before the boiler before the boiler equipment maintenance inspection, as in normal shutdown program is stopped, slow cooling, water circulation and ventilation through the furnace, and gradually lowering the temperature of the boiler furnace. When the temperature dropped below 80 ℃, the door opening open various checks on the boiler. Prevent steam, hot water or cigarette burns when opening the door opening. (2) Steam test boiler feed water, should be separated from the sewer line with the respective other operation of the boiler. Blind for a separator plate should be sufficiently strong to avoid high pressure medium in the broken drum is operated. This clearly indicated the blocking position. Combustion chamber and the flue (3) Check the boiler should be separated from other operation of the boiler. Flue and ventilation doors must be closed tight after separating. 2, preparation of the pressure vessel (1) before the container inspection prior to examination, to be completely cut off the connection tube between the container and the gas pressure or other equipment, particularly equipment using flammable or toxic media. Not only must the valve is closed, and must be sealed with blind plates, so that the valve leaks, resulting in leakage of flammable or toxic gases into the vessel, fire, explosion or poisoning. (2) all media in the container to be discharged. Containers containing flammable, toxic or suffocating medium should be cleaned, replaced or sterilized, by sampling and analysis. A power supply associated with the container, such as a container with a stirrer, reversing mechanism, etc., must be cut off, and a clear flag indicating not allowed to connect. 3, a boiler maintenance considerations are (1) Note ventilation and monitored prior to entering the drum, the container, the drum must be opened, all in the hole hand hole in the container and the collection tank, the air convection period and adequate ventilation. When entering the drum and the container inspection, one must monitor the external device. Before entering the combustion chamber or flue must also be ventilated. (2) Note that the detection of electrical safety in wet flue drum and when the lighting voltage should not exceed 24 volts, with electric lighting. In dry flue, using appropriate security measures, it may be no more than 36 volts lighting voltage. When entering the test vessel, should be used no more than a low-pressure proof lamp voltage 12V or 24V. When the supply voltage detection equipment and maintenance tools than 36V, good insulation must be reliable grounding cord. Boilers and containers should not be used flame. (3) removably connecting member pressing the forbidden band in the inspection of boilers and pressure vessels, pressure if the fastener member needs to unload or screwing, must fully release the pressure, before it can be. Bolts or other fasteners can not be tightened or unloaded at the boiler pressure, in order to prevent accidents. (4) prohibits self-test instead of the hydraulic pressure to the boiler pressure vessel test pressure test generally use water as the pressure medium, there is no gas as a pressure medium, otherwise it is very dangerous. For structural reasons the like, water can not be used as a pressure medium test individual containers, when instead of hydraulic pressure in accordance with design requirements, should be thoroughly checked before the test, check the strength and reliability of the measures taken. Prior to implementation should conscientiously implement the design in accordance with the provisions of, and prior consent of the security sector.
When the pressure of the steam boiler protection small small steam boiler pressure exceeds the rated boiler steam pressure protection, the need for chain protection: is shutdown, the system stops the combustion; fire mouth can also be varied, single-stage or two-stage combustion, You can adjust the amount of oil, so the buck, to ensure the safe operation of the boiler. Fuel (gas) pressure protection and steam boiler water, as the use of multiple protection: the pressure controller typically use two pressure controller, the pressure signal converted to an electrical signal, the electromechanical converter, the function of the high pressure, or low levels of signal The electrical switching loss, external circuits or automatic control chain protection. Common pressure controller and pressure gauge, vapor pressure overpressure alarm can cut off the burner limit is reached; pressure controller adjusts single fire or dual fire burning the actual operating pressure; for large burner, the pressure may be adjusted according to the size of the size of the amount of fuel, and always maintain a stable pressure relief valve operation is the last line of defense to protect the boiler, the boiler pressure exceeds the limit, according to the set pressure relief valve design feature, the exhaust pressure relief, to ensure the normal operation of the boiler. Temperature protection temperature protection is an important procedure in the safe operation of the boiler, is particularly important for the regulation and protection of the boiler temperature steam; at the same time to regulate protective role in over-temperature hot water boiler sellers. Conventional boiler temperature protection means is a bimetallic temperature controller.