Dairy production and processing sectors, need a lot of steam on food drying, sterilization, stereotypes, such as processing, steam 2.5mw coal fired duel fuel water tube boiler essential. Xinjiang Ake Su Xinnong Dairy Co., Ltd. as a local brand, has a large market users. 2016, Akzo increased demand for dairy production, the original steam boiler company can not meet today's production needs. In the same year, Akzo dairy cooperation with our company, signed a series SZS 6 tons of steam pipe steam boilers, steam support for the dairy industry dairy production Aksu.
Main steam 2.5mw coal fired duel fuel water tube boiler temperature abnormal phenomenon of how to do 1, main steam temperature anomalies alarm. 2, the rapid variation of the main steam temperature, a secondary damper frequently significantly reducing water operation. 3, starting superheat outlet steam separator above or below normal. 4, if the steam with water, the unit will water shock occurs. 1 reason, the fuel and water supply imbalance, the separator outlet temperature abnormality. 2, coal combustion conditions change or affect, such as excessive load lift; and pulverizing mill administration system abnormality stop; means automatically increase or decrease the failure rate is too large amount of wind and the like. 3, the central flame furnace changes, such as the bottom seal damage, W and inadequate flame downstroke. 4, the control failure by warm water, warm water flow rate reduction is abnormally reduced or increased. 5, feedwater temperature mutation. 6, does not match the wind coal. 7, the secondary combustion heating surface. 8, furnace coking or fouling seriously. 9, heating surface leakage squib. 10, flue gas damper opening degree is not normal. 11, coal sudden change occurred. 12, the uniformity of the powder feeding substantial change occurs. 1 process, failure caused by unit coordinated coal - water ratio should be immediately released coordinate offset, in accordance with the current load demand, with reference to the start of the steam superheat separator, and adjusting the amount of fuel corresponding to the amount of water, with one, two main desuperheating water rapidly steam temperature control in a normal range; when the coal - water ratio should avoid imbalance after coal and water while adjusting; when coal - water ratio is adjusted to further adjust the load after a relatively stable; contact maintenance processing timely. 2, when the water supply system fault condition occurs a significant disturbance furnace should pay attention and automatically coordinated working conditions, so as not to manual intervention, when not working properly coordinated and automated, should be manually adjusted, stable water flow, referring to separation according to the water flow steam superheat, the adjusted amount of fuel, with a secondary spray water rapidly controlling the main steam temperature within the normal range; contact maintenance processing timely. 3, due to rapid changes in load caused by the load change rate should be adjusted; load change caused due to protective operation or the like caused by heat load to be quickly adjusted to maintain the boiler pressure of the main steam stability. 4, by warm water automatic dysregulation, should be appropriate Save warm tone is switched to the manual may be an intermediate point of the feedwater control system be corrected for temperature if necessary, or the feedwater to switch control to manual control, due to lower lifting and lowering the load speed to prevent steam temperature, promptly contact a service process. 5, the boiler furnace cause severe fouling and coking of the main steam temperature anomalies can be corrected by an appropriate degree of superheat outlet steam separator start, adjust, and in a timely manner and the furnace heating surface sootblowing. When the platen superheater sootblowing or superheater outlet temperature is still above normal and a secondary reducing water damper fully open, to check the furnace and the combustion air distribution system is normal, the checking process to reduce still overtemperature unit load. 6, flue gas damper adjusted to an appropriate opening degree. 7, if the bottom seal after losing back to normal immediately. 8, to strengthen the turbine expansion, differential expansion, axial displacement of the shaft vibration and bearing temperature monitoring, if abnormal, the process according to the corresponding regulations. 9, after the above measures, if invalid, should immediately drop the load process. 10, in front of the main steam temperature main steam 50 ℃ drastically reduced within 10 minutes, should an emergency stop.
The working principle of hot water boiler is very simple, which depends on the heat energy of fuel combustion to achieve the function of heating water, it is a kind of simple heat energy boiler. Hot water boiler is one kind of boiler, mainly because its medium is hot water. There are many kinds of hot water boilers, which can be divided into point hot water boilers, oil hot water boilers, and some more environmentally friendly gas and coal fired hot water boilers according to the fuel used.
1, while maintaining the original nominal parameters of the boiler (e.g., steam temperature, steam pressure, water temperature, etc.) remain unchanged, maintaining or improving output and efficiency of the boiler.