Around at 10:12 on February 28, 2019, Zhangjiakou City Chabei Management District Kai Austrian Energy Management Services Ltd. Taiwan 15 tons of steam biomass boiler drum due to the control zone tearing a serious accident, killing three people the death of four people were injured.
Currently seven injured in hospital emergency treatment, cause of the accident is still under investigation, rehabilitation disposal is also an orderly manner.
Heartbreak is that similar incidents happened from the last time, only 28 days.
At 15:30 on January 2019 May 2009 55 points, Zhangjiakou City Hall Ltd. Hong Mei generating boiler scalding accident, three people were killed and one injured.
Boiler special equipment is clearly defined our country, whether it is manufacturing, purchase, installation, operation or maintenance, have strict operating guidelines. Now many have adopted new boiler intelligent control, operational safety compared to conventional boilers, more convenient; but that does not mean foolproof, vigilant and master the correct method of application, in order to minimize accidents frequency. After all, the cost of each accident are living lives.
Recalling these events boiler explosion
March 3, 2014, Xingtai City, Hebei Province, a steam boiler explosion. Boiler plant razed to the ground, surrounded by multi-family residential buildings, factories affected by the explosion were destroyed. According to the injured introduction, cause of the accident may be due to faulty boiler and pressure control instruments not work, the pressure continues to rise, leading to an explosion.
November 15, 2014, Wangcun Daiyue located in Tai'an City, congee shop offices under Daiyue Xiaoxiang Court Food Co. boiler explosion accident caused part of the building collapsed, the scene four different degrees of harm employees .
About 5 minutes, packaging wood factory near Jincheng territory of Huai'an City, Jiangsu Province, south of the village of Hope Town boiler explosion occurred at 9:00 on January 24, 2016.
February 28, 2016, after the city of Hebi in Henan Province Junxian Pi Mao Shan Street office building energy source of the village cents Ltd. boiler explosion occurred, resulting in many injuries and death.
May 12, 2016, hurt Fengxian Plastics Corporation boiler explosion occurred, resulting in many casualties.
Boiler plant in Henan What are the advantages of industrial boiler manufacturing industry in the middle of our country is a very wide range of common industrial equipment. The main boiler is a thermal energy supply device consists of two main parts consisting of pots and oven, and is widely used in many areas of residential heating and chemical. Market now above the boilers are more buyers prefer purchasing goods and services in the middle of a good boiler plant in Henan Province, the Henan Boiler Plant these particular what are the advantages? First, with advanced production equipment and complete production equipment, excellent evaluation test or not is a manufacturer of industrial importance. Henan boiler plant with more advanced production equipment to ensure that the products produced have relatively high quality. It also has a high level of operating welding equipment and advanced computer-aided design and a series of related equipment. Second, have a varied product has a very long history of manufacturing the type of boiler boiler plant in Henan, Shandong gas boiler is very comprehensive. Henan Boiler Plant is capable of producing good quality hot water boilers and various gas boiler in line with national environmental standards. Also different types of dealer steam boiler industrials, oil-fired boiler and boiler oil boiler and many other products are also included. Third, the product has a unique feature of good service Shandong gas boiler has determined the need for customers to buy after a series of work before they can be put into use after including the safe transportation of goods and the correct installation and commissioning, and many other work. And a very good market reputation boiler plant in Henan Province has a very good quality and after-sales service attitude. Overall boiler plant in Henan Province has been able to win the widely popular among consumers in the market, depending on the characteristics of the advantages detailed above in Henan Boiler Plant owned by these three aspects. That is, complete with advanced production equipment, we can produce various kinds of products as well as different types of boiler can provide good after-sales service.
How to observe whether dealer steam boiler industrial is short of water and how to deal with itSteam boiler is a kind of energy conversion equipment. The energy input to the boiler is chemical energy in fuel, electric energy, heat energy of high temperature flue gas and so on. After boiler conversion, steam, high temperature water or organic heat carrier with certain heat energy is outputted out. Water level below the minimum safe water level, or invisible water level, water table glass tube (plate) appears white. The two-color water level meter shows all the gas-phase indication colors. Low water level alarm signals occur in high and low water level alarms. Low water level interlock device, water level below the specified value should stop the operation of fan, induced fan, grate reducer motor. There is also a sharp rise in superheater steam temperature above the normal outlet Steam temperature. The exhaust temperature of the boiler rises. The feed water flow rate is smaller than the steam flow rate, if the furnace tube or coal economizer tube rupture cause water shortage, the opposite phenomenon will occur. When the water shortage is serious, you can smell the scorching smell. When water shortage is serious, red water wall tube can be seen from the furnace door. When the water shortage is severe, the furnace tube may break, and a burst can be heard, steam and smoke will be ejected from the furnace door and the fire door. By calling water; for severe water shortage, it is necessary to stop the furnace urgently, and blindly feed water to the boiler. Reduce fuel, blast, draw wind, and supply water slowly when water is classified as a slight water shortage.
Steam and hot water boiler water level gauge fault safe hydraulic machine operating company of Henan fast boiler with small series to introduce a common dealer steam boiler industrial water gauge Problem safe operation of steam and hot water boiler water gauge failure of hydraulic machine, the causes and solutions approach a hot water boiler steam water gauge reason and common problems: 1, the water level is too low mounting table; 2, water table, even the water pipe is too small; table 3 have low level or a water level indicator, when active, only one only water table; 4, the ground water table, drain cocks no drainage; 5, a drum water level on the table is valid, another water table damage; 6, the tap water gauge screw fixed; 7, the tap water gauge leak, leaking; 8, the performance of the water table level false; 9, the drum water level in the water table irregularities two inconsistent; water gauge glass often broken; 11, water level gauge glass without guard; 12, water gauge low water level glass plate not shown in the red line instructions; 13, glass plate dirty water table, the water level observation is unclear. The main reason is because of 1-4 above design, installation or alteration of dislocation caused. When the steam boiler with a low water table position when the drum is only a case of the water table, water table because the internal balancer lowland leakage short-circuit (at that time can not be detected), resulting in the emergence of lowland water table high water level ( the so-called full of water), and the water table on the drum performance but low water level (or even probably not see the water level), then the fireman because they can not determine the true level of the boiler will go immediately and check the water level in the drum on the table, it will be very serious water shortage in container delays when the boiler accident occurred. Glass-sided water table in front of a glass sheet metal frame box lined with asbestos pad contact surface made of cardboard and then screw the cover frame and the cover pressure closely. Some even show the water level too low trust status of the water table, and take a little sewage, mistakenly steam boiler water when filled with water incident handling, accelerate the production of the accident, there is precedent for such incidents to be investigated. Then, the above-mentioned reasons hinder 5-9 problem occurs mainly boilers lasting not run when washed in water table, not routine maintenance, resulting in water gauge cocks rust, gas, water and even the block, or insufficient packing or aging deterioration. False water level phenomenon, in addition to gas, water or even the cock pipe is blocked, but also could be vapor, the water pipe connected to the water table caused by misalignment connection; steam, water tap handle installed the wrong position resulting cock closed, since there poor water quality, the boiler priming and thrown false water level. Water gauge glass is broken mainly steam, water faucet centerline not aligned, the presence of glass bending stress; long glass without expansion gap; water table is at the window glass is a cold draft, and the glass pipe quality was poor. Safe operation of hydraulic machine 1, hydraulic machine operator must be trained to master the equipment performance and operating techniques to work independently. 2, before the operation, you should clean up various debris on the mold, wipe any dirt hydraulic rod. 3, the mold must be installed hydraulic machine in case of power failure, and prohibit the collision start button, the lever foot on the footswitch. 4, installed on the upper and lower dies, the die gap adjust, unilateral allowed off-center, a good confirmation of the fixed mold pressure again. 5, before the hydraulic machine is first started working apparatus idling 5 minutes while checking whether enough oil tank, pump noise is normal, the hydraulic unit and pipes, fittings, if the piston leakage phenomenon.