Such as hotel Home Hotel Group is one of the three major brands, in 300 cities in the country has nearly 2,000 hotels. Home Inns has won China Golden Pillow Award for Best Chinese economy hotel chain brand award, in 2014, Home Inns brand value of $ 420 million of selected China's top 100 brands. April 4, 2016, BTG hotel groups such as the privatization of the hotel purchase transaction has been completed delivery. In mid-2016, as a Beijing hotel with our preliminary communication, the urgent need two boilers work of heating and hot water supply. I related technical engineers and recommend it to calculate the number and size of the boiler on the hotel room as hotel Willy sharp V6-99 two models.
Effect of boiler fine coal combustion boiler operating principle is to use thermal energy or heat in industrial post fuel released by combustion is transferred to the water in the container, the temperature or pressure of the water reaches a certain desired steam heating equipment. Many people will feel that coal-fired boiler more detailed the better, but is it really? From a combustion point of view, the finer coal particles more easily form a good mixing with the air, the more complete the combustion. But the coal particles too small, for boilers, milling power consumption will be greatly increased. Industrial boiler, the coal into the furnace too small, there will be the following questions: 1, coal leakage losses, etc. from grate gap increased. 2, boiler grate to be at full speed, power consumption increases. 3, fly ash, fuel loss increases. 4, a coal burning ember i.e., unstable combustion, furnace volume heat load difficult to sustain stable. So the boiler when using fine particles of coal, coal is subject to how much water, raw coal water, play groups and then into the furnace. If the burning coal of 8 to 12h before the water, so that the penetration of moisture into the interior of the coal particles is better. Water vapor produced is moistened triatomic gases, flue gas can strengthen radiation, facilitate ignition, exhaust and reduce heat loss
How to provide boiler thermal efficiency thermal efficiency of the steam boiler has the following methods: low-pressure boiler at the factory has been designed considering the problem of thermal efficiency of the boiler, the flue gas from the device or change little aspects of energy-saving possibilities, it is best to start from the energy-saving operation (here talk recovered water vapor condensation method). The current design thermal efficiency of domestic low-pressure boiler is generally 70 to 90%, generally the actual operation of the thermal efficiency of about 60 to 80%, some even below 50%, a small low pressure industry as long as the operation, maintenance properly, can meet the design thermal efficiency of manufacturers. I think the management and operation should pay attention to the following points: First, the boiler flue gas temperature monitoring. Typically the maximum exhaust heat loss is loss, it is important to good control of exhaust gas temperature, exhaust gas temperature is generally low pressure coal-fired boiler of 150 ~ 180 ℃, fuel boiler exhaust gas temperature is 210 ~ 240 ℃, so when the boiler to find out why when the exhaust temperature is too high and promptly eliminated. Coal-fired boiler flue gas temperature is too high reasons are: high furnace pressure; shorting smoke; thick soot on the heat pipe; thick scale pot like. High temperature fuel exhaust reasons are: 1 air not adjusted oil, the oil is not completely burned in the chimney the secondary combustion occurs aft; 2 soot too, the need for timely cleaning; 3 shorting smoke; 4.... thick scale; Second, controlling blowdown rate. Without restricting the general rate of industrial sewage control in 5 to 10%, in the pot of water to ensure that qualified (mainly total alkalinity and pH value), the blowdown rate as low as possible, the sewage to adhere to the "ground row, row less, are ranked "the rules. Third, the maintenance of good furnace wall insulation. The heat loss is also a relatively large heat losses, now the manufacturers in the manufacturing and design has been well thought out, so we do not need to change, we just trying to be difficult to maintain. Outer surface temperature generally does not exceed 50 ℃, it will have to find out the reasons such as too high, and remove. Boiler insulation should always be kept dry, for coal, not a long positive run, or easy to damage the coal furnace wall and gate and so on. Fourth, adjust the ratio of fuel and air volume, complete combustion of the fuel as possible. Generally do not have a small amount of wind testing instruments, we can only go by experience adjustment. For oil, the normal combustion flame was yellow-white, non-glare, flame stability, no visible smoke chimney; For coal, the normal combustion flame pale, no visible smoke chimney, basic cinder burn coal particles as even as possible. Fifth, the need for a sound water treatment. Improve water treatment and water quality testing can maximize prevent fouling and correct guidance of the sewage, but it did not do a lot of small, companies usually do not pay attention.
Coal fired watertube boiler is a type of coal fired boiler in which water circulates in tubes heated externally by the fire. Coal fuel is burned inside the furnace, creating hot gas which heats water in the steam-generating tubes. In smaller boilers, additional generating tubes are separate in the furnace, while larger utility boilers rely on the water-filled tubes that make up the walls of the furnace to generate steam. ZG Boiler manufactures coal fired firetube boiler and watertube boiler for sales. In Aug 2014, our company exported a set of 15 ton SZL coal fired firetube boiler to Thailand, an paper factory. More details about this project, just email me now: [email protected]