Shutdown four tons of gas boiler 0 7 mpa 0 3 t coal biomass fired steam boiler shutdown and maintenance of fire into pressure shutdown, normal shutdown, emergency shutdown. A pressure fire fire shutdown shutdown pressure applied to temporarily stop the supply of steam, the boiler is shutdown pressure hot standby state. 1, before the pressure reduction appropriately to fire the boiler load, and according to the length of the seam thicker shutdown time, (up to 200mm) to accelerate the speed of the grate, the grate is stopped when rotated about 1.5 meters from the coal seam to the shutter. 2, stop blowers, blower suitably adjusted flap subsections, relying on a lean-burn natural ventilation is maintained. 3, the sewage, to allow the water level in the boiler water level. 4, Yang fire regularly, to prevent rotation of the furnace grate extinguish the fire bed. Young fire first before sewage water, then rinse water level gauge. II. Normal shutdown Normal shutdown for heating period ends, boiler pour fire into the buck repair or maintenance. 1, make a record before shutdown problems in operation, so that after the shutdown process. 2, the coal bucket coal memory runs out, the amount of toner to reduce the wind. 3. Stop the blower, draft fan stop and then the opened door grate ash. 4, after the steam supply is stopped out, the boiler to the boiler water to maintain a high level. 5, close the main steam valve, if the pressure rises to open the air exhaust valve suitable pressure relief. 6, stop the water supply to the boiler and economizer attention to monitoring changes in water temperature, open return pipe if necessary. 7, 4 to 6 hours after the furnace fire bed down exhausted, continued rotation of the cooling grate. Throughout the boiler throttle, the door should be kept closed. Allowed to naturally cool. 8, appropriate to open the pump, the boiler water and sewage. When the pressure drops to zero, open the air valve. 9, when the boiler water temperature is below 70 ℃, boiler water can be exhausted. Shutdown is complete. 10, less than 24 hours during shutdown. Avoid Shutdown cooling process, step-down too fast. Third, emergency shutdown emergency shutdown applies to the boiler accident, g combustion equipment damage, furnace or boiler structure collapsed wall is red-hot, a serious threat to the safe operation of the boiler when; h boiler pressure parts found serious distortion, leakage. when i found flue gas explosion or secondary combustion, boiler and seriously endanger the safety of operating personnel;; when endanger the safety of operation.. the safe operation of the boiler j endanger other unusual circumstances when. 2, the emergency shutdown procedures to immediately stop a blowing coal and reduce the wind; B rotates quickly grate, the pour slag pit coal or sand, wet ash coal burning fire to extinguish. , but not to the firebox water;. c boiler air valve, the relief valve opens quickly exhaust the steam pressure is reduced;. d after the fire goes out, stopping fan, opening the ash door and door, promote air circulation accelerated cooling; 3, emergency shutdown Notes a. when an accident and emergency shutdown due to lack of water, boiler feed water is strictly prohibited to, and shall not be such as to open the air valve or exhaust valve work on preventing boiler from sudden changes in temperature or pressure to expand accidents;. b when filled with water due to an accident and emergency shutdown, should immediately stop the water supply, reduce combustion, open the drain valve and drain, due to lower the water level, while opening the main steam pipe, the sub-cylinder and steam traps mother tube, water and prevent steam pipe with a large number of water hammer occurs. c. emergency shutdown operation to ensure the safety of the main event of an accident to calmly deal with, timely reporting, and make relevant records in the "log table boiler." d. Whether shutdown any case, we must maintain timely contact with steam departments.
6 tons gas 0 7 mpa 0 3 t coal biomass fired steam boiler steam pressure adjusting a boiler operation, must frequently monitor the pressure gauge indicated. To maintain stable steam pressure, boiler pressure must not exceed the design pressure. Second, increasing boiler load: Steam pressure decreased boiler load is increased, if the level is high at this time, the amount of water should be reduced to a water supply or suspend, the amount of coal and increase the air volume. Gradually increase the amount of water at the same time to strengthen the burning, keep the steam pressure and the water level is normal. Third, the boiler load reduction: the vapor pressure rises to reduce boiler load, if the level is high at this time, the amount of coal should be reduced and the air volume, reduced combustion. Then the appropriate water reduction or suspension of water supply to the water vapor pressure and stability in the nominal range. Then press the normal combustion and the amount of feed water 8 to adjust. If the actual water level within the boiler is low, to increase the amount of water should, until the water level returns to normal after the combustion and needs to be adjusted according to the water vapor pressure and load changes.
6 tons adjusting a combustion gas 0 7 mpa 0 3 t coal biomass fired steam boiler, normal combustion boiler three basic aspects of indicators include a uniform supply of the fuel, reasonable ventilation, adjustment the combustion. 1, to maintain the high temperature of the combustion chamber temperature of the upper layer is preferably in the 1100 ~ 1300 ℃, flame orange in color. Flame reddish color indicates that the amount is not enough to the wind, the color white indicates that excessive wind. It should be appropriately adjusted. 2, fuel ash to reduce ash content in the combustibles to be below 10%. 3, reducing the temperature of the boiler flue gas exhaust gas temperature should be controlled below 200 ℃. 4, holding furnace negative excess air boiler is 1.2 to 1.4, by adjusting the balance of the blowers to maintain the furnace pressure is -20 ~ -30Pa. 5, the thermal efficiency of the boiler to improve the thermal efficiency of the boiler should be kept above 60%. II. Combustion Adjustment 1, the amount of fuel to air required for combustion and the amount of a reasonable distribution. Ventilation should first increase the amount of fuel increases, it should first reduce the amount of fuel supply reduced ventilation. 2, the thickness of the seam and seam thickness configuration grate speed is 80 ~ 120mm grate speed at high, middle and low profile configuration of several commonly used methods:. 9a rapid combustion of thin seam b c thick seam in low combustion. 3 thick seam combustion speed, the segment with the wind blowing principle: burn promoting intermediate ends. That is, after the coal into the coal starts to warm up the shutter, fire line front arch, the primary combustion zone, the middle grate to burn the rear grate zone. Normal combustion conditions are: fuel from the coal at the beginning of the fire shutter 300mm, uniform flames, the fire bed formation, at the end of combustion from the end of the grate 300 ~ 500mm. 4. maintain proper furnace temperature to avoid coking. The fire bed to maintain the homogeneous combustion, to avoid burning fire bed obliquely. 6. The residence time of the fuel on the grate in less than 30 minutes.
The picture shows the fast boiler processing plant located in the plain areas, plus catch up period is for a residential area of Beijing for the production of low concentration of nitrogen product water tube boiler heating in winter, as scheduled in 2018 to ensure that heating at the same time, to meet the 20 mg / m require extremely low emissions of nitrogen oxides, Beijing air emission standards applicable to other regions 30 mg / cubic meter.