After the boiler put into use, such as the hotel responsible person to give us feedback: fast boiler advanced product design, simple and intuitive operation, the most critical is energy saving, low NOx emissions, can be used in the Beijing area. Compared with other boiler brands, fast Boiler made us worry. --customer feedback
Check Item item hot water boiler hot water boiler comprising a boiler inspection and checking internal use preparations, checking in the furnace and the flue, the boiler attachment check, check automatic control system, the secondary device, check the combustion device, the auxiliary heat check the surface of the hot water boiler must be done before running some tests, these tests are quite a lot of us, it is possible because of our neglect and causing very serious consequences. Therefore, we must forestall, be sure to carefully check the following before the hot water boiler operation. 1, including the use of internal inspection and boiler ready. 2, inspection, and furnace fouling and debris inside the flue in the furnace and flue should be cleaned. Flue duct and damper, the shutter must be complete and compact, flexible switch, opening and closing accurately indicated. 3, check the boiler accessories, check the safety accessory is intact; cock is rotating flexible, easy to use; all kinds of instruments and controls should be complete, good, clean. After passing the examination, should the gauge cocks in working condition. 4, check the automatic control system. 5. Check the accessory device. 6, inspection of the combustion apparatus, the combustion apparatus is intact inspection; mechanical transmission system, coal handling system, the ballast system test switch normally; spring-loaded safety level of a gearbox should be appropriate, well lubricated; coal shutter indicate the correct scale. iron eagle neat, well, turn the ballast plates full, flexible movement. 7, the auxiliary heating surface of the inspection, check the auxiliary device (fan, blower, pump, etc.) are firmly connected coupling; proper belt tension triangle; oil should be good enough; cooling water flow. After passing the examination, installed security guard, respectively, commissioning, and note the current when idling. It is fed out of the hot water boiler heat equivalent to a mass per hour (usually expressed in tons) in water was heated from 20 ℃ and heat output of all vaporized into a coal fired hot water and steam boiler water absorbed three expressions, in tons) water from 20 ℃ heated and vaporized into all heat absorbed by the steam boiler it is fed out of the hot water heat equivalent to a mass per hour (i.e. typically kcal / hr (kcal / h), tonnes / hour (t / h ), megawatt (MW). (1) kcal / h is in metric units of expression, which represents the heat of hot water boiler fed out per hour. (2) t t borrowed steamed steam boiler popular argument, ( 3) megawatts (MW) is the international system of units unit of power, the basic unit is W (1MW = 106W). this expression formal documents should be used.
Horizontal coal fired hot water and steam boiler accident treatment method: 1 overpressure accident boiler, boiler overpressure phenomenon of (1) a sharp rise in steam pressure, the pressure exceeds the allowable working pressure gauge pointer over the "red line" safety valve operating pressure is still elevated. (2) the operation of the device is the interlock overpressure protection, should send overpressure alarm signal, stops the air blowing, the wind, coal. (3) steam temperature and steam flow rate reduction increases. 2, to treat boiler overpressure (1) weakened rapidly burning, manually open the valve or bleed valve. (2) increase the water supply, while the lower reinforcing blowdown drum (It should be noted at this time to maintain the normal water level of the boiler), in order to reduce the temperature of the boiler water, thereby reducing the pressure in the boiler drum. (3) as a safety valve malfunction or all of the pressure gauge damage, emergency shutdown, safety valves and pressure gauges are to be repaired after the boost operation. When endanger the safe operation of (4) Boiler excessive pressure, blood pressure should take measures, but too fast buck is strictly prohibited. (5) boiler overpressure eliminate serious, to the shutdown of the boiler internal and external inspection, to eliminate the overpressure caused by deformation, leakage and other safety accessories and maintenance unqualified. 1, the phenomenon of the boiler water (1) below the minimum safe water level line, or no visible water, the water table glass (plate) as a white. (2) as a full-color water level gauge vapor instruction color. Low water level alarm signal (3) water level alarm occurs. (4) low water interlocking means, the water level should be below a prescribed value blower, Fan, grate reduction motor stops running. (5) a sharp rise in the superheater steam temperature, higher than the outlet steam temperature. (6) boiler exhaust gas temperature rises. (7) the water flow is less than the steam flow, causing Should the water tube due to tube cracking or economizer, an opposite phenomenon occurs. (8) When a serious water shortage, can smell the burnt smell. (9) When a serious shortage, the door can be seen from the red-hot waterwall tubes. (10) a serious water shortage, the furnace tube may rupture, then can hear the explosions, smoke and steam from the door, watching spray the fire door.
Auxiliary means configuration of the auxiliary boiler apparatus comprising a boiler fuel supply means, air blowing means, the wind means, water supply means, means ash, dust removal device, instrumentation, valves and other automatic control device. Today small to introduce a boiler with auxiliary devices. A boiler fuel supply role is to store, transport, supply of the fuel. There are coal, to the media devices (mill, of mill, and coarse powder separator and lose powder duct), and supply means (for the fuel heater and the like), a gas supply device and the like. Air blowing means which effect a treasure ah blower and duct, the grinding media and air into the furnace through the air preheater apparatus. Blower apparatus, comprising a draft fan and the smokestack, speaking furnace flue gas to exclude air sent. Water supply means comprises a water tank, water supply pipes and water treatment equipment, boiler feed water away. In addition to ash means ash comprising artificial addition, other mechanical ash, ash in addition to water, in addition to the negative pressure pneumatic ash, soot blowers, and other field ash, ash from the boiler and out away. Dust removing device, which includes a variety of dust action of gravity, inertial force, centrifugal force, washing bar-type, sound wave, filtering, static electricity, etc., fly ash out of the boiler flue gas, to protect the environment. Instruments, automatic control devices and valves, including the role of pressure gauge, a thermometer, a water level gauge, the alarm level, the relief valve, water meter, steam flow meter, pressure meter, indicating the exhaust of carbon dioxide and other instruments, a steam valve, a valve, a check valve, like the valve discharge valve, and automatic detection, automatic protection, control and automatic adjustment and automatic computer control means. The boiler more safe, economical operation. These are the auxiliary device structure of the boiler, I believe you must have learned a lot of knowledge of it, I hope this helps you make better use of boiler equipment.