Horizontal coal fired steam boilers 10t accident treatment method: 1 overpressure accident boiler, boiler overpressure phenomenon of (1) a sharp rise in steam pressure, the pressure exceeds the allowable working pressure gauge pointer over the "red line" safety valve operating pressure is still elevated. (2) the operation of the device is the interlock overpressure protection, should send overpressure alarm signal, stops the air blowing, the wind, coal. (3) steam temperature and steam flow rate reduction increases. 2, to treat boiler overpressure (1) weakened rapidly burning, manually open the valve or bleed valve. (2) increase the water supply, while the lower reinforcing blowdown drum (It should be noted at this time to maintain the normal water level of the boiler), in order to reduce the temperature of the boiler water, thereby reducing the pressure in the boiler drum. (3) as a safety valve malfunction or all of the pressure gauge damage, emergency shutdown, safety valves and pressure gauges are to be repaired after the boost operation. When endanger the safe operation of (4) Boiler excessive pressure, blood pressure should take measures, but too fast buck is strictly prohibited. (5) boiler overpressure eliminate serious, to the shutdown of the boiler internal and external inspection, to eliminate the overpressure caused by deformation, leakage and other safety accessories and maintenance unqualified. 1, the phenomenon of the boiler water (1) below the minimum safe water level line, or no visible water, the water table glass (plate) as a white. (2) as a full-color water level gauge vapor instruction color. Low water level alarm signal (3) water level alarm occurs. (4) low water interlocking means, the water level should be below a prescribed value blower, Fan, grate reduction motor stops running. (5) a sharp rise in the superheater steam temperature, higher than the outlet steam temperature. (6) boiler exhaust gas temperature rises. (7) the water flow is less than the steam flow, causing Should the water tube due to tube cracking or economizer, an opposite phenomenon occurs. (8) When a serious water shortage, can smell the burnt smell. (9) When a serious shortage, the door can be seen from the red-hot waterwall tubes. (10) a serious water shortage, the furnace tube may rupture, then can hear the explosions, smoke and steam from the door, watching spray the fire door.
After use throughout the winter, the Central Conservatory of Music give us feedback, six V6-99 fully meet the heating needs of the school. And boiler fuel and water requirements are not high, urban water and low-pressure natural gas combustion can operate. The most important point is that nitrogen oxide emissions are very low and very happy to recommend it to others to do the brother of boiler units. --customer feedback
Distinction gas coal fired steam boilers 10t and a conventional coal-fired boilers and gas steam boiler (1) in a conventional coal fired boiler should be prechamber through grinding equipment, coal should be produced for combustion injected into the furnace, the entire combustion process in furnace and in the form of a suspension. (2) as long as the gas steam boiler biomass fuels open, dried and crushed, the helical feeder to the air before it is blown into the top of the combustion grate vibration. After burning the soot removed from the baghouse gas steam boiler. 2, different air supply preheating. Gas-fired steam boiler burner underlying mode, two-pass configuration, the fuel combustion, the boiler operation is stable and take up less space, while the spoiler is inserted smoke tube, smoke slow speed, increase heat transfer, a high thermal efficiency, reducing user fees (1) coal-fired boiler air preheater flue at the bottom, below the economizer; using flue (2) temperature of the air supply end of the cigarette is heated, different from a conventional boiler, the feed gas steam boiler air preheated by the air preheater flue gas cooler and the two parts to feed water as a medium to absorb heat of the flue gas, conveying air into the furnace. Warm air supply system for a gas steam boiler is controlled by adjusting the supply air temperature of the heating water flow can be provided by adjusting the electric charge of the bypass track circulation water through the valve and the air preheater flue gas cooler bypass control. Water heat exchange section, cooling water heated through the air preheater and the cold air delivery fan; then, this part of the water continues to flue gas cooler, flue gas by exchanging heat with water in the flue gas cooler, water heating, cooling the flue gas. In the bypass, a bypass flue gas cooler and another bypass air preheater, both have their own electrical control bypass and isolation valves. When the flue gas cooler exit gas temperature is too low, the bypass isolation valve is opened, water does not pass through the flue gas cooler, flue gas heat exchanger is not performed to ensure the flue gas cooler outlet gas temperature is not too low smoke corrode gas cooler. In order to enter the flue gas cooler feedwater temperature is not too low, when the air preheater outlet water temperature is below a certain temperature, it opens the bypass, supply cool air can not be heated, the water temperature is too low to prevent the influence of the flue gas cooler work . But also to ensure the temperature of the flue gas through a gas steam boiler precipitator. 3. The coal-fired boiler flue gas fired boiler bag filter should be used for desulfurization libraries to ensure the emission of pollutants lower than the standard. Steam boiler is an energy conversion device, the energy input to the boiler fuel chemical energy, electrical energy, thermal energy and other forms of high temperature flue gas, and after converting the boiler, the steam output having a certain outside thermal energy, high-temperature hot water or an organic carrier. Gas hot water boiler with environmental protection, energy conservation, safety, salient features fully automatic operation, and ease of use. In addition, due to the operation of the economy, government policies to encourage, gas hot water boiler more and more people of all ages. However, biomass combustion flue gas are different. Biomass fuel of low sulfur and nitrogen content, only through the biomass filter before discharge into the atmosphere. However, the carbon content of fly ash produced by the combustion of biomass, coal-fired boiler boiler efficiency is better, but the carbon dioxide content in the greenhouse can be reduced. Under the same nitrogen content of the fuel, the nitrogen oxides emission concentration of boiler far below the emission standards for coal-fired boilers. The problem should be noted that operation of the gas boiler. From the operational perspective view of the gas boiler, the operation of the gas boiler should note the following: The actual fuel consumption of the boiler operation, the amount of oil to the adjustment screw feeder. Unburnt fuel in the furnace, induced draft fan and the blower can not be stopped. Sudden power outage in operation, must be promptly removed fuel furnace. Not add biomass fuel before the shutdown. When the furnace stopped, there is no need of the bank up a fire. When the fuel on the grate exhausted, drum induced draft fan may stop running. If you want to know more about boiler, gas steam boiler, you can log on to our website, we look forward to your call!