3. High efficiency, energy-saving, security: design the over-temperature, over-pressure, water, leak detection, flame, etc. a variety of protect features, make sure the safe and reliable boiler operation.
6 tph SZL biomass-fired boiler project for wood products industryWood processing is molding the wood under the action of a mould after being softened, bending the curve shape that the design requires, the following procedure is drying and shaping. In this case, wood cannot be heated and shaped by fire, therefore, heating and softening the wood by steam has been the only choice. Jiangsu Hongya Wood Industry Co., Ltd. is mainly engaged in producing, processing and selling wood and wood products. There are a mass of wood pellet and wood chip residuals during the processing; Hongya Wood has always been insisting on making good use of waste materials and using these wood residuals as boiler fuel. Due to the high moisture and low calorific value of the wood pellets and wood chips, the problems of low combustion efficiency, ash accumulation and abrasion are inclined to happen. The new generation biomass-fired boiler, which is designed and developed by ZOZEN, has optimized the design of the feeding hopper, the length and width of the fire grate, rotary speed of gearbox, 1st and 2nd air ratio, vapor orientation and position, etc; these methods not only take the lead in solving the above problems, but also ensure the full combustion and the thermal efficiency can reach up to 88%; in addition, ZOZEN biomass-fired boiler adopts appropriate heat resisting grate bars, which effectively improve the reliability of the boiler and ensure the stable running of the boiler for a long time.
Fault boiler long, short sootblower: sootblowers is essential for an important part of a boiler, its role is to purge the ash heating surface, heating surface remains clean, in order to improve the heat transfer effect, to ensure that the thermal efficiency of the boiler, to prevent the heating surface of the coking device. It points both long and short, then, the next will come to tell you what it's common faults and solutions: 1, long soot blower common failure symptoms: (1) failed to start and soot blower soot blower is not from the back. (2) leakage into the boiler soot blowers. (3) at the inner tube was sealed severely sootblower steam leakage, water leakage poppet valve lifting rod. (4) steam inlet flange sootblower steam leakage. Analysis: (1) the control part of the fault. (2) motor failure. (3) firing barrel deformation or Jam. (4) damage to the valve body and the valve seat surface binding. (4) sootblower boiler tubes, damage to the poppet valve packing. (5) an inlet flange sootblower graphite spiral wound gasket failure damaged. Treatment: (1) an electric contact personnel check and control system of the expansion power supply line La on whether the device. (2) an outer barrel furnace boiler sootblower bending portion rapidly burn local manual hand-crank or exit from the barrel as the slide bearing support readjust and corrected barrel, the barrel as serious deformation should be replaced with new of. (3) isolated after the individual valve lift system maintenance, disassembly of the poppet valve and the valve seat and the valve body is polished with a special tool maintenance, such as severe damage to the valve seat or the valve body and replaced. (4) the inner tube packing isolated after replacement of individual systems, note moderate tightening gland studs. (5) to replace the gasket flange. Preventive measures: (1) strict inspection process. (2) to strengthen the inspection, to detect problems in time.
To support employee innovation, the company took out more than 5% of sales each year for technical innovation and product transformation, and the establishment of the Innovation Award and a special incentive fund, for practical gizmos and patented the invention of employees monthly reward. Today, the company has obtained 107 national patents.