To enhance the thermal efficiency gas boilers What environmental policy: the combustion efficiency of combustion represents the degree of complete combustion. To improve the combustion efficiency of gas boilers and environmental protection, we must try to adjust the combustion conditions and better organization of the furnace, fuel combustion, reducing q3 and q4. Gas boiler environmental protection reduce exhaust gas temperature: at present China's industrial boiler flue gas temperature is high, is one of the main reasons of the low gas boiler thermal efficiency and environmental protection. Each small boiler flue gas temperature decreased 15-20 ° C, 15 ° C decreased every large boiler, a 1% increase in the thermal efficiency of the boiler gas. Accordingly, to try to reduce exhaust gas temperature flue gas heat recovery, reducing heat losses q2, the fuel savings. Softened water supply and condensate recovery: boiler feed water softening treatment and condensate recovery measures is to improve the thermal efficiency of the boiler. Raw water contains various impurities and fouling material, if not the water treatment boiler fouling. Low thermal conductivity of the scale, so that once the heating surface fouling due to increased thermal resistance, gas boiler output decreased to increase coal consumption, reducing the thermal efficiency of the boiler. Boiler keeps running at rated load: When natural gas boiler overload, due to the amount of fuel to be increased, the coal seam thickened, grate speed, air volume must be increased to meet the increased load required. Thick coal seam and grate faster incomplete combustion of the solid increase in losses due to increased air volume, the short residence time in the furnace flue gas, some burning of combustible gas has not finished on the drain with the flue gas, so incomplete combustion gas heat loss is increased. Meanwhile, when the overload operation, since the furnace temperature is increased thickening seam, exhaust gas temperature increase accordingly, so that heat loss is increased. Boiler low load operation, the amount of reducing gas, the furnace temperature is lowered, deterioration of the combustion conditions, incomplete combustion loss q3, q4 is also increased. When the boiler load is only 50%, due to a significant reduction in temperature in the furnace, it is difficult to maintain stable combustion furnace. Low load operation relatively increased heat loss, the overload or low-load operation the boiler will result in reduced thermal efficiency of the boiler. Strengthen the insulation, sealing, anti-leakage, anti-risk: Due to the wall gas boiler, soda temperature heat pipe system is better than the boiler room air temperature is high, so that part of the heat pipe system and soda furnace wall to radiation and convection to the loss of ambient air, heat radiation loss becomes the boiler. Only the furnace heat of the heat loss, reduces the temperature of the furnace at the same time, it affects the combustion. Therefore, the use of advanced insulation materials to strengthen the walls and heat insulation boiler pipes, reducing heat loss and improve the thermal efficiency of gas boilers and environmental protection. Temperature and security issues to resolve gas china horizontal water tube coal fired steam boiler
The partnership, fast boiler for the user responsible attitude to have left a deep impression on our fireman boiler operation is not very skilled, fast deliberately sent a party of professional and technical personnel for our on-site supervision of installation, commissioning and training to ensure that the latter can operate our good boiler fireman. --customer feedback
To overcome the steam requirement of the textile processing, textile mill coal fired boiler adopts advanced technology home and abroad and the pilot industry installed 10 ton per hour coal fired boiler to replace carbon intensive furnace oil. Our process heat equipment are used in food processing, chemical, plastic and textile industries.
After the gas hot water boiler hot water boiler vaporization emergency 1. Vaporization handler circulating pump stops abnormally pump failure caused by: ① blower stops running immediately. ② immediately open the door, take measures to pressure the fire, lift the chute gate, cutting off the supply of coal grate. ③ In the case of boiler pressure not greater than 0.6MPa (600KPa), the exhaust valve to follow, only a sharp rise in pressure in the boiler deflated, used only relief exceeds 0.9MPa, and the exhaust process to be carried out slowly, prevention boiler due to loss of pressure and more violently again vaporized. ④ close the boiler water, water main gas valve. ⑤ open stop valve recirculation line, to ensure that the water supply pipe velocity convection heating surface (economizer) to prevent re-vaporization of the economizer. ⑥ The operation of the above operation, at the same time to pay the boiler to reduce the boiler water temperature and the furnace pressure. ⑦ After the boiler pressure is normal, i.e., opening the standby circulating pump, into the normal combustion. 2. Treatment failure or sudden loss of power boiler vaporization of power: ① immediately open the door, lift the coal chute slide gate to take pressure fire measures to reduce the oven temperature. ② Grate with the fastest speed in order in the shortest time to fire onto the slag tap. ③ the degree of treatment in the first case. Once a short time can not supply heating network system, antifreeze should take emergency measures. 3. Due to excessive heat boiler boiler vaporization process: ① the immediate closure of the drum, induced draft fan. ② immediately open the door, take measures to pressure the fire, lift the supply of coal chute slide gate, off of coal, while the grate into fast gear. ③ In the case confirmed the presence of water, the boiler can supply water to the boiler body, boiler out of the water while closing the main valve. ④ Open line stop valve recirculation pump to ensure water velocity convection heating surface of the pipe, to prevent the economizer again vaporized. ⑤ Open circulating pump with jog mode, jog each time less than 30 seconds, again less than one minute jog interval. Jog purpose is to reduce the boiler water temperature, while preventing a large amount of steam into the pipeline system. ⑥ back into place after the safety valve, circulating pump running, and then the normal burning stove. 4. Water boiler system run vaporization process due to water loss, loss of pressure caused by: ① immediately closed drum, induced draft fan. ② out of the water while closing the main valve and the boiler circulating pump. ③ take the same measures to cool the furnace tube described above. ④ Open stop valve recirculation line. ⑤ rely exhaust valve until the safety valve back into place. ⑥ until the boiler water temperature drops below 50 ℃, when the temperature of the furnace temperature less number 200 ℃, again within the boiler feed water, water course to be carried out slowly, to prevent harm to the boiler when the temperature is too large. ⑦ After processing leakage fault, the system time to the replenishment, and out of the water boiler always open the valve, and the circulating pump, and then normal combustion.